Question about AO Smith Pool & Spa
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
your looking at $175-$225 for just the single phase motor depending where you purchase, I just replaced mine(identical unit) due to screaming dry bearings, if you replace it your self make sure to keep new wires tight along side of unit or fan will cut them if loose and its a fan- 5mfd/25mfd compressor@440volt cap
Posted on Sep 27, 2009
Testimonial: "Thank you, you gave me exactly what I asked for. Now I can shop wisely. Tim"
AO Smith will send you a manual. Contact info http://www.aosmithmotors.com/contact/contactform.aspx?ekmensel=fb5d653b_6_16_btnlink
Posted on Apr 21, 2010
Does the motor data plate say anything about the motor. You can hook up a motor like yours with 3 wires. First use an ohmmeter and check the resistance between the brown/white wire to the black then the yellow wire. The resistance between brown/white and one of the others should be pretty much 0 ohms. If not check between the brown wire and the black and the yellow. Which ever wire has 0 ohms with the brown/white wire is the common leg. You can put a wire nut on the brown/white, it will not be used. Next the brown should be for the start winding and the other wire left over will be the run winding. Then connect the common to L2. L1 will go to the run winding and one side of the capacitor and brown will go to the other side of the capacitor. I hope this isn't too confusing. Let me know if I need to explain it better.
Posted on Jun 09, 2010
Testimonial: "Thank you very much for your help-I had the motor leads reversed and when I placed the brn/white to the common on cap like someone else had instructed it of course shunted out and blew the fuses in the disconnect. I used my meter(duh) and switched the motor leads. We got air!! THANK YOU!"
Tips for a great answer:
Jan 05, 2015 | Heating & Cooling
Mar 05, 2013 | Hayward 2HP Pool Pump Motor A O Smith...
Jul 22, 2012 | AO Smith Lennox Furnace Motor P-8-6426 3/4...
May 14, 2012 | AO Smith A.o. Smith Orm5458 1/3 A 1/6 Hp,...
Jul 06, 2010 | AdobeAir Mobile Swamp Evaporative Air...
Jul 04, 2010 | Mastercool Portable Air Conditioner
Feb 19, 2010 | AO Smith A O Smith Motors A O Smith 2hp...
Sep 27, 2009 | Goodman CLQ36AR49 Air Conditioner
40 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: