Question about Rinnai Heating & Cooling
Posted by Anonymous on
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
I'm picking up a faint propane scent when the heater is completely turned off. When I turn the heater on it lights fine so I don't suspect it's the pilot light. Is this an issue with the installation of the fuel line, or could it still be the pilot? Any ideas on troubleshooting the source?
Posted on May 26, 2008
SOURCE: my rinnai 556fa propane heater
I had the identical trouble with my Rinnai 431F just now & read the unanswered posts.
I checked my intake & exhaust & found them connected & intact then went out to check the exterior vent assembly. The "bell" or dome was almost entirely clogged with ice.
I suspect the 60 - 76 lights flashing means insufficient combustion air.
Anyway, I took a hair dryer to it & in 10 minutes it was working as well as ever.
This won't help you October posters but if anyone else has this problem in the future I would start with the outside vent assembly. Get a good look right up inside because I would have missed this ice if I didn't get up close with a flashlight.
Here's a good source for manuals too...
I'm going back to bed.
Posted on Dec 22, 2008
Sounds like it is reaching high limit...either the filters on the back are plugged, or the manifold pressure isn't adjusted properly. IF the exhaust were plugged on the unit, it wouldn't fire at all, since it has a pressure switch to verify vent flow. The slightest blockage, the unit will lock out to prevent damage to the unit.
Posted on Sep 14, 2009
SOURCE: Hi, I have a Nobo electrical
take the panel out pick up the feed cables ,then hot wire them direct to the feed via the thermostat so it works as a conventional heater .its these made in china chips ,useless
Posted on Jan 08, 2011
Tips for a great answer:
Jan 18, 2018 | Rinnai Water Heaters
Feb 14, 2017 | Rinnai Water Heaters
Jul 18, 2011 | Rinnai Vent Free Gas Heater/: 6,000 BTU...
Jun 03, 2011 | Rinnai Heating & Cooling
May 11, 2011 | Rinnai Heating & Cooling
Sep 12, 2009 | Rinnai Toyostove Direct Vent Heater:...
Jul 07, 2009 | Rinnai RHFE-1004FA 38,400 BTU Energy Saver...
Feb 18, 2009 | Rinnai RHFE-1004FA 38,400 BTU Energy Saver...
May 03, 2008 | Rinnai Vent Free Gas Heater/: 6,000 BTU...
Nov 10, 2007 | Rinnai EnergySaver 556 Air Conditioner
50 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: