Question about Heating & Cooling
Check to see if contactor is pulling outside. Pull the cover off to see if contactor has pulled in. You may have bad contactor,capacitor or no power to the outside unit. Check breaker. Sometimes there is a float switch inside that may be tripped.Russ
Posted on Jul 26, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jul 28, 2016 | Haier Heating & Cooling
Dec 19, 2010 | Intertherm P3RA-036K Air Conditioner
Apr 05, 2010 | Heating & Cooling
Mar 16, 2010 | Carrier 38CKC042 Air Conditioner
Aug 06, 2009 | Heating & Cooling
Aug 02, 2009 | Ruud UAKA060 Air Conditioner
Aug 02, 2009 | Heating & Cooling
Jul 08, 2009 | Heating & Cooling
May 26, 2009 | Heating & Cooling
33 people viewed this question
Usually answered in minutes!