Question about Goodman Heating & Cooling
Either the thermostat, fan relay on circut board or blower motor bad. Jumper the R and G terminals together on the circut board, depress the door switch and see if the blower runs, if not, check for power to motor, capacitor and motor windings. If it runs then you have tstat/control voltage wiring problem.
Posted on Jul 26, 2009
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Dec 26, 2015 | Goodman Heating & Cooling
Jul 13, 2011 | Heating & Cooling
Jan 02, 2011 | Goodman CLJ30AR32 Air Conditioner
Aug 08, 2010 | Ruud Handle Air Conditioner
Aug 05, 2010 | Heating & Cooling
Jan 12, 2010 | Carrier XQB101D Air Conditioner
Mar 28, 2009 | Carrier Heating & Cooling
Jan 19, 2009 | GE Zoneline AZ38H12DAD Split System Air...
84 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: