Question about Traulsen Freezers
Probably not. you would need to change the expansion device. You could probably get as low as 15-20 degrees but I doubt you could do much more than that without some system changes.
Posted on Jun 19, 2017
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
if compressor is running, then you are correct in saying no point in replacing stat. by sounds of it you have a faulty compressor fault or a syatem fault - impossible to dignose by remotely. this is not a diy job i'm afraid
Posted on Jul 25, 2007
The first place to look is to check the charge. Using guages check the low and high side pressures and their relationship to one another. I'm assuming your unit is a R-404 unit which, if fully charged and the condenser is clean, and the fan is operating, should have about 210 to 250 high side pressure. Other things to check: evaporator coil ice/frost free; defrosting properly to obtain a clean coil; all evaporator fans running. If low side pressure is above 30 PSI you have a weak compressor. Whatever, fix the Traulsen unit, its head and shoulders above anything else on the market today.
Posted on Nov 24, 2008
Sorry, no secret. The fan wasnt working so we called an engineer who bypassed a sensor. Now it works perfectly again.
Posted on Mar 23, 2009
The refrigerant level is low. The only thing is that the unit may not have a low charge. There can be several things that cause the unit not to refrigerate properly. It could have weak valves in the compressor or even a bad TXV(thermostatic expansion valve). Have you had this box repaired yet.? I see that this is an old post.
Posted on May 15, 2009
Tips for a great answer:
Feb 25, 2013 | Traulsen Reach in Freezer - G22010
Sep 08, 2011 | Traulsen 46 cu. ft. / 1303 liter...
Dec 16, 2010 | Traulsen 24.2 cu. ft. / 685 liter...
May 20, 2010 | Traulsen 46 cu. ft. / 1303 liter...
May 16, 2010 | Traulsen 24.2 cu. ft. / 685 liter...
Aug 19, 2009 | Traulsen 7 cu. ft. / 198 liter Commercial...
Aug 19, 2009 | Traulsen 24.2 cu. ft. / 685 liter...
Dec 09, 2008 | Traulsen 24.2 cu. ft. / 685 liter...
Dec 11, 2007 | Traulsen 7 cu. ft. / 198 liter Commercial...
180 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: