Question about Dryers
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: I have to change the
Posted on Jul 02, 2008
Incoming white - outgoing white
This is the neutral, which just passes through without connecting to the switch
incoming black - switch black the hot wire provides power to the switch
switch red - outgoing red a traveler, will have power when toggle is one position
switch yellow - outgoing black
the other traveler, will have power when toggle is in the other position
incoming bare - switch green - outgoing bare the switch is grounded and it passes through
If this was helpful, please vote.
Posted on Mar 23, 2010
SOURCE: 120v hot tub wiring diagram
I would expect your tub is either 110 or 220. Currently you are set up for 110. Based on that ... you disregard the red wire.
If your tub can run on 220, you should run it on 220 as this is more economical.
You should probably have an electrician check this out and make any changes to assure proper and SAFE operation of your tub. You are using a GFI, correct?
Thanks for your interest in FixYa.com
Posted on May 16, 2010
GE 15086 is a 7-day programmable timer. It has more wires than spring-wound timer because clock motor runs on 120V circuit, just like ordinary electric clock. The clock on spring wound timer operated by a spring.
If I understand correctly, the old timer has 2 wires. One of these wires is the Hot wire ... and that wire will connect to GE timer black wire.
The other wire from old timer goes to Load ... and that wire will go to GE timer red wire.
Instructions on a lot of these timers say, it timer doesn't work, then reverse the two wires described above ... this is because timer only works when Timer black connects to Hot.
You can also turn on power and test each wire that came off old switch to bare ground wire. When tester lights up, that is Hot wire.
GE timer Green wire connects to bare ground wire.
Moving on to GE timer white wire. This wire is necessary for the clock to run. This wire connects to Neutral wire which is usually white. You can test for Neutral by testing Hot wire to each white wire in box ... when tester comes on, that is Neutral.
If you do not have a white Neutral wire, then connect GE timer white wire to bare ground wire. This is not code, but it will work fine until you hire electrician to run Neutral into box.
Posted on Oct 04, 2010
Tips for a great answer:
May 30, 2015 | Atwood GCH10A-4E GCH10A4E Gas and Electric...
on Mar 07, 2010 | Garden
on Dec 28, 2009 | Hardware & Accessories
Mar 14, 2015 | Pool & Spa
Sep 27, 2014 | Saws
Jan 02, 2014 | Heating & Cooling
Jul 09, 2010 | Heating & Cooling
Dec 23, 2009 | Intermatic T103 Indoor 120-Volt 40-amp...
Jul 20, 2009 | AO Smith 1 1/2 HP 115/230V 56C Replacement...
Jun 04, 2009 | Home
22 people viewed this question
Usually answered in minutes!