Question about Carrier Heating & Cooling
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Hi, You say that it will light and then shut-off when the ELECTRIC pilot shuts off? If it has an automatic pilot ignition, it wouldn't have a thermocouple? It would have an ignition module with a flame sensor. Could you check this for me and let me know which one you have for sure? I can help you out better if I knew. Thank you and please get back to me.
Ps If it is electronic, there will be a flame sensor mounted next to the pilot. It has a ceramic body with a metal rod coming from the end.You can take a piece of steel wool not sand paper and clean the metal rod (sensor). The pilot flame will surround this keeping the burners on.After cleaning it, and if the pilot continues to go out, I would say that you're ignition module has an intermittent internal problem, and needs to be changed.
Posted on Oct 31, 2009
That blinking light may be the diagnostic light. Count the blinks next time it fails. Carrier units will have two different blinks depicting the error code such as one blink followed by a pause than 3 blinks giving you an error code of 13. Then look at the wiring diagram, it will have an error code chart telling you where to start with your diagnosis. You already know that if you remove the cover it erases the error code, so look thru the small window first.
Posted on Dec 01, 2009
Tips for a great answer:
Sep 10, 2015 | Home
Feb 18, 2015 | Carrier Heating & Cooling
May 12, 2017 | Heating & Cooling
Nov 30, 2009 | Carrier XHB123D X/Y Series Heat/Cool Air...
Oct 06, 2009 | Carrier XHB123D X/Y Series Heat/Cool Air...
Mar 11, 2009 | Carrier Heating & Cooling
Dec 21, 2008 | Carrier XHB123D X/Y Series Heat/Cool Air...
Nov 12, 2008 | Carrier XHB123D X/Y Series Heat/Cool Air...
Dec 06, 2007 | Heating & Cooling
Apr 14, 2018 | Carrier Heating & Cooling
34 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: