Question about Electrical Supplies
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: Computer Shuts Down Randomly
is the fan running.... check how hot it is on the bottom.... could very likely be thermal shut down... if it gets to hot it shuts down before there is any damage.... see if you can remove the shield around the fan and clean out the dust and dirt and in my case cat hair. if you can't figure out how to get the cover off let me know... i should be able to find the service manual for you
Posted on Dec 19, 2008
SOURCE: Gen. set won't auto start.
This sounds a little like a bad wiring problem between the transfer switch and the generator. But before I leap to any unfounded conclusions let's make sure I understand just which Guardian generator and transfer switch you have. The generator I think you have is an air conditioner sized box that has a 2 cyl air cooled Generac GT990 engine in it. The control panel has a 15 amp fuse, and maybe a 7 amp one, some LED indicators, a 3 position rocker switch (manual,off,auto), and a momentary set exercise switch. If you look inside your transfer switch there is the transfer mechanism, a single relay, either 2 or 4 fuses, and a terminal board where 4 small control wires connect to the generator. The control wires will be labeled N1, N2, 193, and 23.
If all of that is true then I'll also assume that the generator is blinking all of the LEDs and as soon as you put the rocker switch in the manual position the generator starts and the transfer switch moves to the "generator" position. It shouldn't do that, manual means switch the switch manually too. :-)
Let's take care of the exercise setting first. Switch the main output breaker of the generator to the "off" position, this prevents the transfer switch from activating even if the generator runs. Next put the generators rocker switch into the "Auto" position and wait at least 1 minute, if the generator starts we have to fix the wiring between the N1 and N2 terminals in the transfer switch and the matching terminals in the generator before we can proceede. If luck was with us and the generator is just blinking its LEDs at you, press and hold the set exercise switch for 30 seconds, you're reseting a "watchdog" type circut so it has to be for the whole 30 seconds. When you let go of the set exercise switch the LEDs should blink another 10 times or so, then the generator should start and run its exercise for 12 minutes more or less and then it'll shut down. At that time the only LED that should be lit is the green "system ready" one and it should be steadily lit. Remember to close the output breaker again.
Next let's address the transfer switch issue. If I've understood you correctly, the transfer switch moves anytime you turn the generator on. The only reason a regular old RTS type transfer switch could do this is that it's being commanded to transfer. It works like this, the 2 coils that move the transfer mechanism get powered by the source we're trying to switch to, once the switch gets into the position it's going a pair of limit switches disconnect it from the power supply so that the coil is only "live" during a transition. Spring loaded contacts hold the switch in either position once it's more than halfway towards either one. The relay inside the box is also in line with the limit switches so that if the relay is deenergised the switch will try to get to the utility position and stay there, it can't if there is no utility power to drive the transfer coil. On the other hand if the relay is energised, the switch will try to get to the generator position and stay there, if there is no power from the generator it can't because the generator is what drives that bottom transfer coil. So I think that for whatever reason the relay in your transfer switch is staying energized when we don't want it to be.
On the terminal board inside the transfer switch you should see terminals labeled 194 and 23, these are the power to the relay coil (194), and the ground to transfer signal (23). With the generator set to off, and a fairly quiet room, disconnect the wire from terminal 23, if you can hear the relay coil click on and off when you touch the wire to terminal 23 there is something wrong with the wiring at the generator end of things. You should also see 12 volts DC between terminal 194 and ground, this comes from the generator too.
If the relay didn't click back and forth above check it by using a short piece of wire to connect terminal 23 to ground, if the relay isn't energised when terminal 23 is grounded and deenergized when terminal 23 is open you either have a bad relay or a problem in the grounding of your system. To get a bad relay fixed for free call up Guardian, register the generator (you'll need proof of purchase), and get them to tell you where your nearest warrenty service person is. If you tell him about this post he'll bring a relay with him when he comes to you.
If you're satisfied that the relay in the switch is working properly, we're on the trail of a wiring problem at the generator end of things. If the generator has just been installed you should carefully check that wire 23 hasn't been connected to terminal 0 at the generator terminal block. It's easy to get this connection wrong when doing th e install. The other thing that can go wrong is that the wire can get pinched inside the conduit and short to ground. To check this disconnect both ends of wire 23 and measure between either one and ground, you should get nearly infinite resistance.
If you've proved to yourself that all of the wiring is correct, and the generator is properly grounded, you probably have a broken control board in the generator. To get the control board replaced use the same procedure as the relay above.
If that doesn't get this resolved for you post a comment and we'll try a different approach.
Posted on Mar 06, 2009
Hello, between 2001 and 2003 the Volvo clusters were faulty mounted. The fault is in the CPU on the PCB board ( the cold joints ). There is a need to reflow this and the problem will be solved.
( I can make it ;-) and have done a lot of cars ).
For better info, this fault can be worst and worst, later there is Airbag fault, some indicator lamps will turn on and off crazy etc.
Posted on Aug 12, 2009
It could be several things: A faulty crankshaft position sensor, a problem with the ECU, a bad ground, a faulty mass air flow sensor, faulty camshaft position sensor, a bad fuel pump or fuel pump relay. If you have a large chain type auto parts store ex.(autozone, advanced auto parts, pep boys) nearby, once you get the car started you can go there and they have a diagnostic tool that they will hook up to your car and test it for free, It may read some codes that may pinpoint your problem. If no codes come up, I would be inclined to believe it may be a loose wire or bad ground somewhere.
Posted on Feb 01, 2010
Testimonial: "this web site was sooooo helpfull!! best thing ive come across! i'd recomend it to any one, the person helping me was fantastic!"
Mine does the same. I don't know what it is. It's not that it's frozen up because every program I'm running continues to run and when I press the power off button it brings up the choices to turn off restart or stand by.
Posted on Oct 01, 2010
Tips for a great answer:
Aug 18, 2013 | Briggs & Stratton Manual Start Home...
Aug 22, 2011 | 2001 Chevrolet Blazer
Oct 05, 2017 | Kohler 12 kW Emergency Power System -...
May 25, 2010 | Sharp 32C-240 32" TV
May 05, 2010 | Kitchen Appliances - Others
Jan 17, 2018 | 1999 GMC Suburban
Nov 12, 2009 | Briggs & Stratton 12,000 Watt Bi Fuel...
Aug 08, 2009 | Kohler 12 kW Emergency Power System -...
Jul 18, 2009 | 1997 Jeep Grand Cherokee
Jun 30, 2008 | 1998 Oldsmobile Intrigue
65 people viewed this question
Usually answered in minutes!