Question about Hardware & Accessories
I removed the old single toggle switch, then connect the wires (ground, white-white, red-red, black-black). While the timer can turn the light on and off, it does not keep time (i.e., the dial does not rotate). Suggestions?
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
You will have to have schematics from the old wiring diagram. Then you will have to confirm its consistency with actual old wiring before you can be sure that the wires run to the proper places on the old heater and a/c system. This sounds like a gas furnace and is simpler than a heatpump. Once you know what distinguishes the wires with the same color, you should label them and then you may call them a different color if they were wired with wrong wire colors. You may be in luck if you go to the furnace control box an look at the terminals.. They are usually labeled with a R for Red and W for white and Bl for Blue and B or Black. If you have other colors on these then it sounds that it was wired with wire spare wire by someone who knew what they were doing but neglected to leave a path for someone else follow.
You may be able to use a continuity tester of circuit tester to id these wires that are in question...
ie, once indintified, you can match with the requirements of the new stat.
Posted on Jan 13, 2009
SOURCE: Wiring a ceiling fan w/light
To add to red54's comments:
This is what I believe you have:
- one source in the ceiling box (black & white)
- one donwline circuit in ceiling box going to another wall/ceiling box (black&white)
- on switch wire in ceiling box coming from your wall switch (black & white) -- this is the white wire which will be hot when the switch is truned on
Here's how it should be connected:
- all 3 blacks in ceiling box connected together -- no other wires in this bundle
- white wire (which is hot when switched) coming from switch connects to the black/blackwhite fan wires
- connect all reamining white wires together in bundle
- connect all ground wires together
It's that simple. Trick is figuring out, of the three cables in the ceiling box, which is source, which is downline, which is switch.
Maybe red54's procedure can help you figure that out.
Posted on May 11, 2009
remove white switch one and connect to incoming white ground--all whites should be connected [hooked] together these are grounds-- switch 1 black from fan ,leave switch 2 red from fan ,switch 3 vanity black
Posted on Feb 22, 2010
HI .. if the switch has only a black and white wire attached, and there are no other wires in the wall box, then you cannot use this timer switch. You need to return it and get a timer that does not use a neutral connection. The wires you have are a switch leg from the light and there is a white wire but it is not a neutral.
If there are other wires in that wall box , tell me and we can chat more about how to remedy this .
Please Vote !!
Posted on May 25, 2010
SOURCE: I have purchased a Utilitech
What you have a single pole light switch you are replacing with the timer. As you say you have 2 black wires. One black wire is the incoming power wire and the other black wire goes up to the light. On a normal single pole switch is makes no difference which of the screws you connect it to. Of course with the exception of the ground screw. Tie all the white wires back together that are in the wall box and shove them to the rear as they are not needed to make this connection. The correct connection is to connect one of the black existing black wires in the wall switch box to the black wire on the timer. Now connect the other black wire to the blue wire on the timer. The red wire is not used in a single pole connection and is only used in a 3 way switch connection, so just put a twist connector on it and shove it back in the box. To recap, connect black wire on timer to either black wire in box. Connect the other blue wire to the other black wire. Do not use the red wire. Hopefully you did not hurt the timer by connecting it incorrectly. If it does not work after setting the timer up according to the instructions you have ruined the timer by wiring it incorrectly. Hopefully no damage has been done.
Posted on Aug 14, 2010
Tips for a great answer:
Mar 13, 2017 | Hardware & Accessories
Dec 05, 2014 | Hardware & Accessories
Nov 13, 2014 | Hardware & Accessories
Oct 04, 2014 | Hardware & Accessories
Aug 14, 2013 | Defiant Timers: 5-Amp In-Wall Digital...
Dec 26, 2010 | Leviton 6230M Decora Four Preset...
Nov 28, 2010 | Intermatic Inc. ST01C Digital In-Wall...
Sep 15, 2010 | RTO Amertac TEO5W Decorative Indoor Weekly...
Apr 08, 2010 | Pass & Seymour / Legrand D703P Harmony...
Sep 04, 2009 | Heavy Duty Intermatic Wall Switch Timer...
59 people viewed this question
Usually answered in minutes!