Question about GE Hardware & Accessories
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Go to electricalexpeditors.com
Posted on Dec 30, 2009
Testimonial: "thank you very much for your responce. I had tryed the paragon website and it was very little help to me. I have found the correct trippers now."
First this model is a 230V model I believe. That means the motor runs on 230V. IF it's working when it's "ON" then you probably have a line and load set of wires reversed. Look at your wiring diagram. I believe 1 and 3 are line and 2 and 4 are load. Since the timer motor is connected to term 1 and 3 it should receive power at all times. When the switches trip then 1 is connected to 2 and 3 is connected to 4. If I don't have the numbers right on your model, you can see the two small wires from the motor. These should both be Line on a 230V model.
Posted on Jul 03, 2010
1) Clock motor needs replacement:
Link below shows timer and wiring manuals.
2) 120Volt Clock motor sells for $43 at Frontier lighting
3) New Tork 1103 sells for $55. Just swap out insides without changing box.
4) Intermatic crossover for Tork 1103 shows Intermatic T103 timer.
Amazon sells T103 for $50
Add a comment for more free help.
Also take advantage of fixya phone service.
For a price, expert speaks with you over phone while you work on timer or any do-it-yourself project.
Fixya is always less expensive than a service call.
Posted on Jan 23, 2011
With the Intermatic timers I'm familiar with, pulling out the dial but, if it pulled out and turns to lock, make sure you have it back the way it was. Obviously the time is doesn't matter because you are using it manually. Anyway, the dial shouldn't really effect the manual switch. If you disconnected any wires or if any came off , you will need to put them back. The system is pretty simple, just like a house switch. It sounds to me like the breaker is tripped or a wire came off.
Posted on May 13, 2011
Tips for a great answer:
Jul 03, 2014 | General Electric GE 56941 24-Hour Outdoor...
Jul 24, 2011 | Kitchen Ranges
Jul 12, 2011 | Intermatic & Indoor/Outdoor Rain Tight...
Jun 02, 2011 | General Electric GE 56941 24-Hour Outdoor...
Feb 23, 2011 | Hardware & Accessories
Feb 08, 2011 | Intermatic & Indoor/Outdoor Rain Tight...
Dec 28, 2010 | Intermatic Mechanical Timer Switch - Pool...
Nov 25, 2010 | Intermatic WH40 - Water Heater Time Switch...
Nov 20, 2010 | Intermatic T103 Indoor 120-Volt 40-amp...
Oct 24, 2010 | Intermatic T104 24h 208-277v Mechanical...
55 people viewed this question
Usually answered in minutes!