Question about Kohler Electrical Supplies
Check diodes on main control board. they short out if something went wrong.
Posted on Nov 08, 2017
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
New users get 2 Free calls (no credit card required) and instant help on almost anything you can think of (from cars to computers, appliances, handyman, and even pets).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
When this happens, this usually means that your genset is not creating voltage. First thing I would do is disconnect your remote start wire from the genset, this will eliminate the start switch inside the RV. For a shorted remote start switch can cause you genset to shutdown. Second, place a volt meter at a spot where you will be able to read genset voltage. If no voltage is available and your voltage regulator is new, then the problem is with either the rotor or stator. The rotor is the easiest check. You need to reach the brushes. Take a resistance reading, which should be around 20 ohms. Clean the rings and make sure there is enough length on the brushes, at least over 1/2". Next, flash the fields using a 12Vdc battery. Use rubber gloves when doing this. Place the positive side to the ring closest to the bearing and negative goes to the back ring. This is done while genset is running so be careful with rotating parts. Have a volt meter on the output wires. Once you flash the fields the voltage should increase to over 50Vac. If it does then your stator is bad since you installed a new voltage regulator. If the voltage does not increase when flashing, then the rotor is bad.
Posted on May 09, 2009
SOURCE: RV Onan Emerald 1 Generator
Check all the ground wires and make sure their not broken or loose. If the wires are good next check the neg. Wire to the coil. Too check the swiitch make sure you have continuity too all the post when the switch in the on position, this requires removing the switch.
Posted on Mar 15, 2011
Tips for a great answer:
Apr 28, 2016 | Kohler Electrical Supplies
Sep 21, 2015 | Electrical Supplies
May 24, 2014 | Kohler Electrical Supplies
Mar 24, 2014 | Onan Generator, 6500W, LP Vapor
Jan 03, 2013 | Kohler RXT-JFNC-0200A-QS 200 Amp...
Jun 11, 2012 | Electrical Supplies
May 09, 2012 | Kohler 12 kW Emergency Power System -...
Jul 23, 2010 | 1992 Volkswagen Passat
Sep 24, 2009 | Kohler Electrical Supplies
Apr 10, 2009 | Electrical Supplies
169 people viewed this question
Usually answered in minutes!