Question about Honeywell Heating & Cooling
Yes that is correct. White and black go to your aux terminal. Then be sure you are setup for heat pump with back up electric heat.
Posted on May 08, 2017
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
For Trane sytems, B is your "Common" wire. O is your reversing valve relay, G is your fan, Y is your compressor contactor, R is Hot, Brown will not be used on your electronic tstat. X2 is your backup electric heaters. Without knowing what terminals are on your new tstat, I cannot offer more information than this. The installation manual may indicate what each terminal is controlling. I strongly suggest to write down ALL of the terminals and colors from your old t-stat and be sure to turn off the power to your air handler. Put the fan switch on your tstat to ON before turning off the power. Make sure the fan is running. Then turn the power off to your Air Handler. If your fan stops running, you have turned the power off to your tstat and are ready to start replacing it with your new tstat. I hope you find this helpful. Good Luck!!!
Posted on Feb 07, 2010
SOURCE: need wiring help for replacing
I am not sure of what help you need on it but here are the most common wiring on a stat
RC=Hot (24v for Cooling)
RH= Hot (24v for Heat)
O= Reversing Valve (Heat Pumps Only)
Hope this helps
Posted on May 11, 2008
Sad to say but you have bought an non compatible thermostat, what you need is a thermostat that has "Heat Pump" somewhere on the package, Honeywell makes those also in the same models, sometimes they can be tricky if your not looking. It should also say 2heat, 1cool too. Hope this helps and good luck!
Posted on Jul 14, 2010
Tips for a great answer:
Aug 06, 2014 | Honeywell RTH6350D1000 5/2Day Prog...
May 27, 2014 | Honeywell RTH6350D1000 5/2Day Prog...
Jul 13, 2017 | Heating & Cooling
Jun 13, 2013 | Honeywell RTH3100C - Digital Heat Pump...
May 23, 2010 | Honeywell Focus 6300B 5-2 Days...
Feb 06, 2010 | Heating & Cooling
Oct 16, 2009 | Heating & Cooling
Mar 22, 2009 | Honeywell Programmable Thermostat Heater
May 11, 2008 | Heating & Cooling
39 people viewed this question
Usually answered in minutes!