Question about Heating & Cooling
If have 25dgs over day should ileave on to low over night to hold heat or turn off and wait to get heat back up
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
locking out, clean flame sensor, metal rod with orange wire run to it located in front of burner farthest from ignitor. steel wool (fine) a couple of strokes and works like magic!!!!
Posted on Oct 22, 2009
Hi, Just to let you know I have repaired central Heat & Air systems for 33 years and Have seen this problem on many occasions. Lets see if I can save you so many trips.It says you have a programmable stat? On this stat and on a mechanical stat, they have what is called a heat anticipator that controls how many and how often your thermostat turns you're unit off and on and how long it cycles after the stat is satisfied. If you have ever seen under the cover of a mechanical stat, ( mercury switch type) you will see a dial with an arrow with numbers as .1, .3, .4 1.0, or .15 to 1.0 amps.Some are fixed and some are adjustable. On a digital stat, you will have to get into the program and see what the heat anticipator is set on. They come from the factory at .4, but to really find out what you'res should be it takes an amprobe to do this. The setting you need is what you're gas valve requires.I am sure I have lost you, but I am just giving you a little food for thought. If you can get into you're program and set this to .4, great. If the problem continues, your anticipator on this stat is more than likely, shorted, which would require you to buy a new stat.With a shorted anticipator, it will seem to be working like you say, but when satisfied, the temp.keeps falling until you reset power, then it fires and repeats this. Change the stat. If this is central heat and air, just follow red-rc which will have a red jumper to rh for heat, white to w, green to g=fan, and yellow or blue to y = cooling. If you have central heat only, you will find 2 wires red and white.Red to rh with jumper still installed to rc and then white to w.This is quite a long explanation, but I wanted you to know a little more then the next guy about your stat. Please let me know.
Posted on Nov 12, 2009
As the weather is getting warmer for many people their freezer and/or refrigerator do not work right because of a dirty condenser coil...
Check out this tip that I wrote about that... it is a great place to start trouble shooting your unit...and something that you can do rather then calling a repair person to do a simple thing for you...
Posted on May 27, 2010
Download a PDF version of the Operating Manual HERE. ___ *Disclaimer: I am not a lawyer, despite the handle. Words to live by: "Every creative act results from a sudden cessation of stupidity." -Edwin H. Land, inventor of the Polaroid Land Camera "The problem can always be solved with the materials in the room." -My college Physics Lab Professor
Posted on Feb 03, 2011
Tips for a great answer:
Sep 21, 2017 | NewAir Heating & Cooling
Feb 04, 2017 | Heating & Cooling
Aug 16, 2014 | Heating & Cooling
Jun 18, 2013 | 2004 kawasaki VN 750 Vulcan
Jun 09, 2017 | Heating & Cooling
Nov 04, 2009 | Heating & Cooling
Oct 27, 2009 | Dimplex DS5603 Heater
Jun 19, 2009 | Heating & Cooling
Nov 01, 2008 | Goodman CLQ36AR49 Air Conditioner
25 people viewed this question
Usually answered in minutes!