Question about Heating & Cooling
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
sometime if the heater has been sitting for days spiders get into the burner area or the area between the tank and the burner and make a web blocking the flow. I have taken a compressed air in a can like the ones you use for computers laptops and blow air up the shaft and around the burner wait 2 minutes then try again. Sometimes it takes 2 or 3 blowouts to work. Put the air compressor right in the little gas nozzle that comes out to light the pilot for the best results
Posted on Aug 21, 2008
Thermo coupler may be defective. it controls the main gas valve by closing main if pilot is out. make sure thermo coupler bulb is positioned over and near tip of pilot flame, but not in the flame. Thermo couplers are inexpensive and easy to change out.
Posted on May 06, 2009
I would change the thermocouple and here is why:
The thermocouple is the pilot's, well, co-pilot! It is the electronic device that senses if the pilot flame is hot enough to sustain burning the gas fuel from the burner. If the thermocouple thinks it's safe, then it keeps open the main gas valve located in the pilot assembly. If the thermocouple does not sense enough heat from the pilot flame (such as when the pilot is out), then the thermocouple shuts off the gas valve to the burners.
How the Thermocouple Works
So what is this thing and how does it work? Well the thermocouple (technically called a thermocouple junction) is a device that contains two metal wires welded at the ends and placed inside a protective metal case. The thermocouple sensor is found at the business end of the pilot flame and is designed to be placed in the hottest part of the flame. The other end is connected to the pilot valve body. As the thermocouple heats up, it produces a small amount of electricity and when it gets hot enough from the pilot, send a signal to open the gas valve by using a solenoid operated by a 24 volt transformer. The thermocouple calls the shots, and by converting heat to an electrical signal, it allows the gas valve to open or close. Once the gas valve is open, gas is then constantly supplied to the pilot and as required for the gas burners (as called for by the thermostat). If the pilot goes out, then the thermocouple gets cold and produces no electric signal to open the gas valve's solenoid and the gas valve shuts off the gas supply to the pilot and burners
Posted on May 27, 2009
Tips for a great answer:
Nov 30, 2013 | Raypak Pool & Spa
Jan 21, 2013 | Napoleon 36" Zero Clearance Top/Rear Vent...
Dec 02, 2011 | Empire Heating & Cooling
Jul 22, 2011 | Uniflame GWT501A Open Flame Patio Heater
May 31, 2011 | Heating & Cooling
Jan 15, 2010 | Kitchen Ranges
Jan 01, 2010 | Cozy Enclosed Front Console Heater 20,000...
May 05, 2009 | Bosch & Tankless LP Hot Water Heater
Jan 15, 2009 | Goodman GMS90703BXA Heater
Mar 08, 2017 | Ovens
Dec 14, 2017 | Honeywell Heating & Cooling
25 people viewed this question
Usually answered in minutes!