Question about Heating & Cooling
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
5 flashing is ' compressor drive' and check the high pressure, condenser fan motor capacitor for proper running
Posted on May 21, 2010
the water comes from the coil, start there make sure there is no obstruction coming out to your condensate line and make sure its properly pitched.
Posted on May 22, 2010
SOURCE: I have a Daikin split
E5 Outdoor activation of compressor over heatprotection or motor lock
Check condenser coil. If dust blocked-clean it.
Check out door fan motor is working. If not replace capacitor or motor.
Check compressor-gradually amps increasing-replace capacitor.
Check for gas pressure. No gas also gives over heat compressor.- Leak test and rectify.
Posted on Jan 16, 2011
Tips for a great answer:
Jul 12, 2014 | Heating & Cooling
Apr 16, 2013 | Heating & Cooling
Jul 25, 2012 | Heating & Cooling
Mar 10, 2012 | Heating & Cooling
Jul 01, 2011 | Heating & Cooling
May 27, 2010 | LG LSC183VMA Split System Air Conditioner
27 people viewed this question
Usually answered in minutes!