Question about Honeywell Televison & Video
There are no LED lights and the whole thing works but its like a buff man with no eyes for comparison
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
should be installed with
1) red to rc and jumpered to rh
2) green to g
3) yellow or blue to y
4) white to w
to test: remove t-stat connect white and red - furnace should operate normally unitil you disconnect.
if it does replace t-stat
Posted on Oct 27, 2009
I would say that you have one of two issues. Either your thermostat is bad or you do not have 24v coming from the heating unit. In this case the problem would be in the low voltage circuit of the heater. At the heater you should have 24v AC when you place an electric meter across the R terminal and the C or W terminal. If you have no vaoltage across the R to either the C or W then you have a bad transformer or a blown fuse in the furnace. If you do have voltage ther and also at the t-stat then the t-stat has gone bad, replace it.
Posted on Nov 14, 2009
SOURCE: display screen has gone blank
You would need to change the screen. Go to a phone repair shop to assist you in changing the screen. It will cost you a little.
Posted on Jun 06, 2010
Tips for a great answer:
Sep 03, 2017 | Honeywell Heating & Cooling
Oct 16, 2016 | Honeywell Electronic Programmable...
May 14, 2013 | Honeywell Rth2310b 5-2 Day Programmable...
Sep 21, 2011 | Honeywell Programmable Thermostat Heater
May 11, 2011 | Honeywell Heat/Cool Thermostat
Nov 14, 2009 | Honeywell Electronic Programmable...
Jun 17, 2009 | Honeywell Focus 6300B 5-2 Days...
May 10, 2009 | Heating & Cooling
Nov 24, 2008 | Honeywell Electronic Programmable...
Jun 12, 2008 | Honeywell Electronic Programmable...
60 people viewed this question
Usually answered in minutes!