Question about Heating & Cooling
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Sounds like bad cold control. Replace it. I cannot see your repyl due to some tech issue w/ the site, so it may be a day or so before I can reply again. Please leave feedback for me if appropriate. Thanks
Posted on Nov 28, 2008
SOURCE: Heat pump cycling on and off.
It sounds as if you you have a low charge of refrigerant, r22. When the unit comes on outside, the outdoor coils become the lowside, there is a low pressure switch that is tripping out contactor protecting the compressor.
Posted on Mar 11, 2009
SOURCE: I have a Daikin split
E5 Outdoor activation of compressor over heatprotection or motor lock
Check condenser coil. If dust blocked-clean it.
Check out door fan motor is working. If not replace capacitor or motor.
Check compressor-gradually amps increasing-replace capacitor.
Check for gas pressure. No gas also gives over heat compressor.- Leak test and rectify.
Posted on Jan 16, 2011
Tips for a great answer:
Jan 28, 2018 | Inverter Heating & Cooling
Jul 20, 2014 | Daikin FDXS12DVJURXS12DVJU Slim Duct...
Dec 05, 2013 | Cars & Trucks
Jan 31, 2013 | Daikin RXYMQ48MVJU, VRV-S Air Cooled Eight...
Jan 16, 2011 | Heating & Cooling
Dec 16, 2010 | Heating & Cooling
Jan 31, 2010 | Goodman Heating & Cooling
Dec 27, 2009 | 1997 Ford Taurus
Feb 01, 2009 | LG LS-K1830CL Cool Mini Split Air...
Jan 03, 2009 | Refrigerators
28 people viewed this question
Usually answered in minutes!