Question about Heating & Cooling
Sadly with the limited information you provide . NO ONE can determine what the problem might be , Suggest you contact a local service company and have it checked by a professional .
Posted on May 02, 2017
What gas unit???????
Posted on May 02, 2017
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Sep 22, 2014 | Lexus IS 250 Cars & Trucks
1. Thermostat calls for heat. 2. Draft inducer motor starts. 3. Pressure switch attached by a small plastic or rubber tube senses the negative pressure produced by the draft inducer and closes. 4. Draft inducer runs for 30 seconds to a minute before you hear a gas hissing sound. The ignitor did not glow, the flame sensor (a small metal probe about 1/8" in diameter, with a white porcelain base) does not sense the flame, so after 8 to 10 seconds the hissing sounds stops with no ignition of gas to heat your home. Your furnace shuts down and goes into a lock out condition until you turn your power switch back off and on again. Then the sequence starts all over again with no ignition of the gas. Solution:You probably need to purchase and install a new ignitor. I would suggest that you inspect your ignitor closely for cracks. Make sure you do not touch the ignitor with your bare hands. If you do not visually see a crack, then you could have a furnace control board problem or a limit, rollout switch problem. The furnace's control board might not be supplying the voltage to the ignitor.If your furnace lights and the gas stays on for 8 to 10 seconds, then shuts right back off, then you need to clean your flame sensor with light sand paper or steel wool. You might need a new flame sensor, but most of the time they can be cleaned an will work well after cleaning.
Dec 11, 2010 | Mr. Heater Natural Gas Garage Heater -...
Dec 06, 2010 | Heating & Cooling
Aug 10, 2010 | Rinnai Water Heaters
Dec 21, 2017 | Brinkmann 815-3786-0 Turkey Fryer
Oct 07, 2009 | Goodman GMS90703BXA Heater
Jul 20, 2009 | Kenmore 74602 Gas Dryer
Jul 14, 2009 | Hayward 100kbtu Pool Or Spa Propane Gas...
May 06, 2009 | Whirlpool LGR5636L Gas Dryer
Jan 17, 2009 | Weather King 10AJA3601AH Air Conditioner
30 people viewed this question
Usually answered in minutes!