Question about Heating & Cooling
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Are you holding the knob for 30 or more seconds,If so,Clean or replace the thermocouple/Flame sensor.
Posted on May 29, 2009
THE flame from the pilot should shoot past the thermo-couple and heat this up and make a small amount of mili- amps to prove the pilot light is lit. ..So if the flame doesn,t go past the thermo-couple it won, make mili-amps or its tme to change out the thermo-couple, They only cost lest than $8:00 and you can change it!
Posted on Dec 22, 2009
Check the following:
See if your heater has a pilot gas adjustment valve. It should be on the gas control valve somewhere. Not all heaters have these. It will be a screw on the valve that can be turned.
Make sure the thermocouple sensing bulb is squarely in the pilot flame and also check that the fitting where the other end of the thermocouple connects to the main gas valve is tight.
Check the pilot gas orifice (where the pilot gas comes out) for carbon build up - you may need to remove the pilot gas line and thermocouple assembly to get to this. This problem is pretty common.
Check the gas pressure to the heater. Run the hot water in the dwelling until the hot water heater starts. Check the flame on the main burner and see what color it is - it should be blue with possibly some yellow-tipped flames. If not, there could be a problem with the gas pressure at the heater or venting. If the heater has a gas pressure regulator, it may be out of adjustment or defective.
Finally, and this isn't very common, the pilot light can be extinguished if there is a draft problem, usually associated with an issue with the flue pipe venting system for the heater or another nearby gas consuming appliance.
Posted on Dec 31, 2009
Testimonial: "thank you. will try these suggestions tomorrow. really appreciate it."
The thermocouple is weak or the pilot needs to be cleaned. If the pilot flame is strong, try replacing the thermocouple which is the tube that the flame burns on runs back to the control valve/
Posted on Jun 20, 2010
Tips for a great answer:
Sep 30, 2016 | Heating & Cooling
Feb 17, 2015 | Rheem Richmond 75 Gal Natural Gas 6 Year...
Jun 14, 2014 | Kitchen Appliances - Others
Mar 30, 2014 | Water Heaters
Aug 02, 2010 | Imperial IFS40 Deep Fryer
Jan 04, 2010 | Cozy Heating & Cooling
Nov 30, 2009 | Cozy (W352E) Heater
Oct 20, 2009 | Amana Comfort Zone 12M32PBEH Air...
Mar 18, 2009 | Pitco Frialator 35CD Deep Fryer
Nov 27, 2008 | Heating & Cooling
Aug 21, 2017 | Heating & Cooling
31 people viewed this question
Usually answered in minutes!