Question about Heating & Cooling
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: Unable To Keep Pilot Light Lit!
I have a Williams top vent gravity wall furnace (model 5009622) and I had the same problem. I had to take the cover off the furnace -- screw on top and two at the bottom (open the access door and there is one screw on each side) to get to the reset button for the vent safety shutoff system. On my furnace it's on the left side toward the top of the unit. I pressed the little red reset button and it's been working ever since. If your furnace is properly installed and doesn't have bird's nest in the chimney, it should work fine. Good luck!
Posted on Dec 06, 2007
SOURCE: Pilot light won't stay lit
Look for dust and lint. Look for them in places where gas should be freely flowing. I had a similar problem with an Empire Corcho wall-mounted propane ceramic catalyst heater. First it was the pilot light, then the #2 ceramic mantle. After horsing around with the gas lines and pressure regulators and trying to re-aim the pilot, it all turned out to be dust and lint in the gas passages. A little dust bunny in the brass pilot tube gave me a pilot light the shape and color of a banana. One puff of compressed air, and I got back my razor-sharp pilot. And some dust in the chimney of the #2 burner kept it burning blue/yellow and blistering paint off the upper surfaces of the heater. A bit of cleaning with a shop-vac put that right. "Passive" heaters are very much prone to this sort of problem because they rely on convection currents (i.e. LOW velocity) to get the job done. Convection currents are notorious dust collectors, as in COBWEB CITY.
Posted on Feb 28, 2009
Probably a bad solenoid in the gas valve. Higher voltage of a new thermocouple keeps it open longer but it still fails over a period of time. Look into a new gas valve for the water heater.
Posted on Dec 17, 2009
There are basically three things that can go wrong with the Warm Morning .
Sensor shut off. There is a sensor button on the back of the unit with a wire going from it to the thermocouple. This sensor turns the heater off if the flue is blocked, however it will also shut the heater off if the wire contacts are dirty, or if the sensor has gone bad.
You can test this by bypassing the sensor. Disconnect the two wires from the sensor and reconnect them directly together. If the pilot stays on, your problem is here. Try cleaning the wire contacts first.
Pilot orifice. If the pilot flame is small and doesnt look healthy, the pilot orifice may need cleaning. The hole is very small and can get dirty. Disconnect the silver tube and clean with electrical parts cleaner. Never try to clean the hole with an object like a pin, you may damage it. You may have to slide out the burner unit to get at the silver tube. (Always shut off gas before disconnecting lines and after you reassemble, spray joints with soapywater and look for small bubbles which may indicate a gas leak. Dont use parts cleaner around an open flame.)
Thermocouple can go bad but this is not as common as the first two problems.
Posted on Jan 28, 2010
Tips for a great answer:
Apr 29, 2017 | Heating & Cooling
Aug 03, 2016 | Heating & Cooling
Jan 14, 2015 | Heating & Cooling
Oct 14, 2014 | Heating & Cooling
Dec 23, 2012 | Hayward H Series Pool & Spa Heater 400k...
Oct 28, 2012 | Heating & Cooling
Sep 20, 2011 | Heating & Cooling
Sep 10, 2011 | Heating & Cooling
Feb 06, 2010 | Vulcan GR45 Deep Fryer
Sep 30, 2008 | Refrigerators
33 people viewed this question
Usually answered in minutes!