Question about Honeywell Humidifiers
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: No water running through the pad
I has same problem and was able to fix ti by taking off the selonoid (cylinder) and then removing both fittings (where the water line enters and then exits the selonoid. The fitting where the water enters has a small pinhole that I found clogged and just cleaned it with a toothpick. After cleaning and reattaching everything, it works fine.
If that doesn't work, you might need a new selonoid which are around $70-$80.
Posted on Dec 08, 2007
I am having the same problem. I have had my humidifier for about 5 years now and I just started having the problem where the water continuously flows through the solenoid. I took apart the solenoid by removing the fittings from both sides. When I did that, I noticed that there was a hole in the metal that allowed me to see through to the other side. Apparently, it had corroded and and broken through, allowing the water to pass through the solenoid without really going through the valve within the solenoid. There are several sites that sell replacements for about $70, which is not cheap, but cheaper than buing a new humidifier for $120. Here is one site I found: http://www.iaqsource.com/product.php/honeywell/32001639-002/?product=112783&category=1142
Posted on Nov 20, 2008
SOURCE: No Water flow thru Humidifier
Loosen the brass fitting where it connects to the soleniod valve. If water comes out your saddle valve is ok. Carefully retighten this fitting. With the humidifier turned on loosen the first fitting down stream from the valve see if water comes out. if it does turn the humidifier off and see if it stops, it should. That will tell you the the valve is ok then, just clean the filter and the oriface. if it does not turn on and off check the wiring. if ok replace the valve.
Posted on Mar 29, 2009
I have the same problem and I have 2 of them fairly new. I can't seem to find out what the problem is either.
Posted on Dec 16, 2010
Tips for a great answer:
Jan 30, 2017 | Humidifiers
Dec 20, 2010 | Honeywell HE220A1019 Whole House...
Jan 09, 2010 | Honeywell Humidifiers
Dec 30, 2009 | Honeywell HE220A1019 Whole House...
Apr 10, 2009 | Honeywell Humidifiers
Jan 19, 2009 | Honeywell HE220A1019 Whole House...
Nov 22, 2008 | Honeywell HE365 Humidifier
Oct 18, 2008 | Honeywell HE220A1019 Whole House...
Nov 30, 2007 | Honeywell HE360A1027 Whole House...
115 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: