Question about Heating & Cooling
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: Power Cord Chew Toy
Any qualified electrician will be able to fix it. It shouldn't take more then 1/2 hour for them do to it, and they can even put on a cable that will protect your dog/the cable from biting through again and possibly getting electrocuted. Overall cost should be less then 50 dollars. Check the Yellowpages if you don't know an electrician.
Posted on Jun 05, 2009
I have a similar situation with 66 a/c units in my motel. The problem is the drain valve in the back of the unit (near the compressor) does not function properly. It is supposed to open when the water temp (laying in the bottom of the unit) gets to 50 degrees cusing the drain valve to open and let the water out. The problem is the water never reaches 50 degrees when the outside temperature is in the 80's. So the water sets in the units. The fan sprays the water over the fan motor, heating element and inside the chasis causing it to rust from the inside out. I have notified LG and they are investigating it...... Amana has the same problems with their units which use the same drain valve and they have removed the drain valve in several motels in the area.
I would suggest removing the drain valve or wedging something under the little round plate so the the unit drains. Also make sure your A/C is tilted properly so the water runs to the back of the unit and drains.
Posted on Oct 09, 2009
Testimonial: "My a/c is still under warranty so LG drilled a small hole in corner of the drain pan on the side where the water was spraying out. Works great now!"
Tips for a great answer:
May 14, 2014 | Haier Commercial Cool 12,000 BTU...
Dec 12, 2013 | GE Zoneline Deluxe Series Cooling &...
Jul 25, 2012 | LG 8000 BTU Air Conditioner w/Remote
May 02, 2011 | Friedrich ZStar ZQ08A10A Air Conditioner
Dec 03, 2009 | Kenmore 8000 BTU Single Room Air...
Jul 22, 2009 | Danby DPAC8020 Air Conditioner
Jul 19, 2008 | Janome Memory Craft 9000 Computerized...
27 people viewed this question
Usually answered in minutes!