Question about Heating & Cooling
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Most likey problem is the diverter valve, not energising fully. This in turn will not move the little plastic lever arm that actuates the microswitch on the side, sending the signal to ignite.
You can buy a diaghram kit from most local plumb centres, you need to replace the diaghram and seals, don't forget the silicon grease to ensure the plunger doesnt stick. Kits less than a tenner.
You should have noticed before it stopped working completely the water had reduced in temperature before the weeks it failed.
To make sure it is a diverter valve fault, depress the microswitch if you can, when the hot water is flowing and hey presto the demand for hot water light should shine.
Posted on Apr 26, 2009
You have a faulty diverter valve, this is a fiddly job, you need to call in a 'Gas Safe' engineer to diagnose and replace this
I hope this helps
Posted on Jul 10, 2009
there should be an overide button on reciever try checking if stat is still communicating with reciever when stat is turned up and down light should flash on reciever
Posted on Aug 17, 2009
Tips for a great answer:
Nov 30, 2017 | Washing Machines
Feb 09, 2016 | Water Water Heaters
Jun 14, 2017 | Water Heaters
Jul 09, 2017 | Heating & Cooling
Nov 18, 2010 | Water Heaters
Oct 20, 2009 | Water Heaters
Oct 05, 2009 | Honeywell Programmable Thermostat Heater
Feb 22, 2009 | Bosch Logixx WFT 2806 Front Load...
Jan 31, 2009 | Honeywell Water Heaters
24 people viewed this question
Usually answered in minutes!