Question about The Video Game Consoles & Games
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Is the condenser fan (outside) turning? You mention that it's hot but don't say if it's turning or not.
These fan motors normally run pretty hot, but not so much that they shut down due to internal thermal overload protectors.
Both the compressor and the fan have termperature overload protectors to keep them from burning out the motor in the event of an overheated condition. The condenser fan must be running or high freon pressure will put an excessive load on the compressor and it will 'kick out' the high-temp overload protector.
Turn off the unit by pulling the outside disconnect (in a small box near the outside compressor unit) or flip the AC breakers in the breaker box. Wait about 30 minutes for the unit to cool off and turn it back on. If the compressor and fan both run for awhile then kick back off, or the fan motor seems to be working under excessive strain, you've probably got a bad motor start condenser (inside the unit) that little round can that is connected through the fan motor wiring. If it's swollen or leaking, it's almost surely defective and even if it's not, excessive load on the motor is a classic sign of a bad start condenser.
You can usually find these at electrical supply stores, well-stocked hardware stores, or most certainly at an HVAC parts house. Be sure to replace the old one with one of the EXACT same value (in voltage and Microfarads (mF) capacity. The shape may be a little different, but as long as the electrical characteristics are the same and is rated at the same or higher voltage than the original, it will work.
Connect the new condenser, mount it to the frame, and restart the unit. This should take care of the problem.
Hope this helps.
Posted on Jun 28, 2009
used parts can be found at junkyards all over the country. they have a parts retrieval system so if your local yard does not have one it can be sent from one that does. lots of folks selling used car and truck parts on eBay and craiglist.
and of course there is always the old google search
that should be more than enough.
Posted on Mar 24, 2011
Hotfrog is a great website that connects people locally withprofessionals to fix things like living room chairs. Here is a link to their site with a searchfor technicians in your area:http://www.hotfrog.com/Products/Furniture-Repair/Regions/Fort-Bend
Posted on May 29, 2012
Tips for a great answer:
Jul 02, 2017 | Garden
May 18, 2017 | Garden
May 28, 2015 | Reptile
Sep 07, 2013 | Garden
18 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: