Question about Heating & Cooling
I just need to know which wires go where on the run capacitor.Wiring diagram is faded inside control panel cover!
3 wires for compressor, 3 for fan. 2 comp. wires go to the top of the contactor, the remaining goes to herm terminal on capacitor. 1 fan wire goes to the top LEFT of contactor, remaining 2 go to com and fan on capacitor. You will then have 1 wire left that goes to the com on the capacitor and should go back to the top RIGHT of the contactor. NOTE: IF YOUR FAN MOTOR IS RUNNING BACKWARDS (MEANING AIR IS NOT BLOWING OUT OR UP) swap the to fan motor wires on the capacitor (fan and com) this should reverse rotation. ALWAYS REMEMBER TO TURN POWER OFF AND DISCHARGE CAPACITOR BEFORE TOUCHING WITH INSULATED SCREWDRIVER. Good Luck!
Posted on Apr 22, 2017
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Aug 25, 2017 | Heating & Cooling
Apr 23, 2017 | Heating & Cooling
Jan 20, 2016 | Gibson Nordyne/2 Ton Heat Pump Package...
Jun 29, 2014 | Heating & Cooling
May 15, 2010 | Intertherm P3RC-030K Air Conditioner
Nov 03, 2009 | Intertherm P3RC-030K Air Conditioner
Sep 16, 2009 | Heating & Cooling
Sep 10, 2009 | Heating & Cooling
Apr 11, 2009 | Heating & Cooling
50 people viewed this question
Usually answered in minutes!