Question about Heating & Cooling
I just need to know which wires go where on the run capacitor.Wiring diagram is faded inside control panel cover!
3 wires for compressor, 3 for fan. 2 comp. wires go to the top of the contactor, the remaining goes to herm terminal on capacitor. 1 fan wire goes to the top LEFT of contactor, remaining 2 go to com and fan on capacitor. You will then have 1 wire left that goes to the com on the capacitor and should go back to the top RIGHT of the contactor. NOTE: IF YOUR FAN MOTOR IS RUNNING BACKWARDS (MEANING AIR IS NOT BLOWING OUT OR UP) swap the to fan motor wires on the capacitor (fan and com) this should reverse rotation. ALWAYS REMEMBER TO TURN POWER OFF AND DISCHARGE CAPACITOR BEFORE TOUCHING WITH INSULATED SCREWDRIVER. Good Luck!
If you need further help, reach me via phone at https://www.6ya.com/expert/thomas_092728000e6acb79
Posted on Apr 22, 2017
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Aug 25, 2017 | Heating & Cooling
Apr 23, 2017 | Heating & Cooling
Jan 20, 2016 | Gibson Nordyne/2 Ton Heat Pump Package...
Apr 11, 2015 | Goodman CKL36AR36 Air Conditioner
Jun 29, 2014 | Heating & Cooling
Nov 02, 2013 | Pool & Spa
Aug 23, 2011 | True GDIM26 Commercial Refrigerator
Dec 16, 2010 | Ovens
Jul 17, 2010 | GE 18 Hp Capacitor Start Ac Motor 115...
98 people viewed this question
Usually answered in minutes!