Question about Nor-Lake Freezer Norlake Refrigeration 8' x 10' Kold Locker Walk-In Freezer - 6' 7'' High w/Floor
My ceiling panel is dripping - I checked conderser coils, look good. The leak doesn't appear to be coming from the clear drain hose; but it is just below it.
The coil in the conditioned space is called the evaporator.
If the water droplets are forming on the ceiling around the evap, it is due, most likely, to the defrost cycle being too long.
Defrost cycle: compressor stops, evap fans stop, electric heaters in the evap come on to clear any ice/ frost on evap fins/ coil.
The ice/ frost melts and some of it turns into vapor. As it hits the cold ceiling surface, it condensates into water droplets. Defrost cycle could be too long. Usually 4 time aday and no longer than 30 minutes should be enough unless there is high humidity.
There could be another cause.
Normally, after a defrost cycle terminates, the evap fans do not come on, due to a delay control. This prevents circulating warm are due to the heaters. The compressor comes on and cools the evap down to, usually 20 degrees or so, and then the fans come on. What could be happening is, the fans are coming on too early and blowing the water driplet off the evap and onto the back wall of the unit.
A third item, is to be sure that the condensate drain is "P" trapped. The prevents warm, outside air from being drawn in and causing exess frost build up, thus excess water and vapor.
Good luck and hope this helps
Posted on Jul 25, 2009
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Jul 08, 2014 | Delfield Freezer 6125XL-S
Oct 23, 2009 | Freezers
Oct 13, 2009 | Freezers
Oct 11, 2009 | Freezers
Aug 30, 2009 | Freezers
Apr 22, 2009 | Hoshizaki Freezer Commercial Ice Machines...
Mar 07, 2009 | Nor-Lake Freezer Norlake Refrigeration 6'...
Feb 12, 2009 | Hoshizaki Commercial Freezer KM-500MAH
Dec 30, 2008 | Kenmore 16.7 cu. ft. / 473 liter Upright...
Oct 15, 2007 | Nor-Lake Freezer Norlake Refrigeration 6'...
303 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: