Question about Heating & Cooling
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
1. Do not set the aircon too low temperature in overcast weather, this will cause ice ups and water dripping. Optimal comfort zone temperature is 24c.
2. You need to open the grill cover on the front of the aircon which unclips either end left and right with a finger pressure. You will find two filters which can slide out and should be cleaned. First tap them together to remove dust, then you can wash them with mild soap and cold water.
3. There is the third possibility that an insect has made a nest in the drainpipe. You should look on the outside of the building and locate a plastic drainpipe. You can either blow into this pipe with your mouth or get a blower. This will unblock any restriction in the drainpipe.
Goodluck and ratemeplease.
Posted on Mar 19, 2009
I've been struggling with this exact error for the past week and fixed it last night. The Error 5 message was misleading in my case and actually was caused by the steam outlet inside the shower and, even after replacing the entire unit and getting the same error, i fixed it in two seconds. Since this was one of the posting i encountered during my frantic searches, i thought i would come back and share my blog posting on this error and my fix:
Posted on Jan 05, 2010
SOURCE: ERROR CODE CH5 AIRCON SPLIT LG
This error is a communication error between your indoor and outdoor unit. You can try turning the breaker off for a few minutes and restart the unit. However if that does not work its best suggested to have an authorized HVAC technician service the unit.
Posted on Mar 12, 2010
E-5 -Comms Error, check your wiring, remove external pumps. Split/Multi - check volts from terminal N to 3 = 0 - 65 Vdc, Multi V - 4 Vdc terminals 3 and 4
Posted on Jan 03, 2011
Tips for a great answer:
Jul 31, 2016 | Heating & Cooling
Jan 23, 2016 | Heating & Cooling
Jan 01, 2016 | DeLonghi Heating & Cooling
Jun 18, 2014 | Samsung AQV36JA Classic 36000 BTU Single...
Nov 06, 2010 | Cfm Daikin R410a Split System Air...
Apr 17, 2010 | LG LS-L1210CL Mini Split Air Conditioner
Apr 05, 2010 | DeLonghi CF210 Portable Air Conditioner
Sep 20, 2017 | Heating & Cooling
22 people viewed this question
Usually answered in minutes!