Question about Heating & Cooling
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
eventually ice freezing evaporator occured two factor you have
dirty fin evaporator and undercharge system.
1. undercharge can easily detected using clamp
ammeter clamp on one line of evaporator while running
read the amper the compare this to yuor service
manual the rated current of the compressor.
2.if the reading current is below the rared current on
manual or there is tag on the body of unit specified
rated current.your unit need to recharge.
if has the same current no change at all freon is still
good, this only need cleaning of eveporator fin.
clean this by pressurise water to purge out all debris
particle on fin tube of evaporator.
cracking sound usally made by blwer or fan
misalignement or distorted bearing blower .
regards have anice day dont forget to rate me.
Posted on Apr 10, 2009
it depends on the distance from main power source # 8 if more than 40 feet look at starting amps then google a wire sizing voltage droop chart
Posted on May 09, 2009
SOURCE: ice formation in the indoor unit
you need to have the unit checked for the amount of freon in the system this must be done with a gauge set the freon amount is obviously incorrect
also the a-frame evaporator must be sealed in the furnace cabinet
Posted on May 28, 2009
Tips for a great answer:
Jun 20, 2016 | Miscellaneous
Aug 05, 2015 | AMVENT 18000 Btu 1.5 Ton Ductless Mini...
Jul 09, 2015 | Heating & Cooling
Dec 28, 2014 | Samsung Heating & Cooling
Apr 10, 2017 | Heating & Cooling
Apr 12, 2013 | Bryant 462AJC021BA Air Conditioner
Feb 18, 2011 | Mitsubishi MSZ-A15NA Split System Air...
Sep 19, 2009 | Heating & Cooling
Aug 11, 2009 | Heating & Cooling
22 people viewed this question
Usually answered in minutes!