Question about Rinnai Heating & Cooling
My heater turns off as soon as the fan starts
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
11 means no gas / failed to ignite - check the bayonet is fully plugged in properly, they can be hard to plug/unlpug - otherwise you wilol have to take it in for service.
Posted on Aug 28, 2009
SOURCE: I have a rinnai energy
Ignition failure caused by either lack of gas, the electrodes are not the correct gap, restriction in the venting system or the spark is grounding prior to the electrodes. Check spark by holding spark wire close to cabinet (1/4"). Check gap across bull horns (electrodes) they should be no more than 3/16. Make sure all gas valves are on and all wires to gas valve are tight. After these checks, you will need a qualified technician to perform some tests on components.
Posted on Mar 07, 2010
Tips for a great answer:
Feb 24, 2015 | Rinnai R85ePLUS Tankless Water Heater
Jun 02, 2011 | Rinnai Heating & Cooling
Jan 18, 2011 | Rinnai Toyostove Direct Vent Heater:...
Jan 08, 2011 | Rinnai RHFE-1004FA 38,400 BTU Energy Saver...
Oct 06, 2010 | Rinnai RHFE-556FAIII 21,500 BTU Ductless...
Sep 22, 2010 | Rinnai Digital Remote Water Heater Control...
Sep 22, 2010 | Rinnai Webstone The isolator EXP tankless...
Feb 15, 2010 | Rinnai RHFE-556WTA Direct Vent Heater NG...
Oct 17, 2009 | Rinnai Toyostove Direct Vent Heater:...
Apr 07, 2009 | Rinnai RHFE-431FAIII 16,700 BTU Direct...
29 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: