Question about Heating & Cooling
What is error code H01 #32 on a Brivis Heater and how do I solve the problem if it won;t clear. The Brivis people told me it was a board circuit board issue but Im sure thats the standard response and somebody knows how to simple fix it.
Thank you !!
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
The heating system has a number of burners which must ignite as soon as the heater starts. When one or more burners does not fully or partially start properly, unburnt gas fed to that burner accumulates in a small pocket until is is eventually ignited causing a small explosion. This condition is caused by restricted/blocked burner jets. The gas jets are small and easily fouled by spider nests or other items sucked into the system. You will need to have the heater serviced by a qualified gas plumber.
Posted on Jun 20, 2009
Error 62 is related to hot surface ignitor (HSI)or/nglo module
you can check the resistance of the ignitor should be less than 10 oms @ 20 degrees
failing that, if you incomming suppy exceeds 270 volt will also result in error 62
Posted on May 15, 2010
Testimonial: "The error did indicate an HSI problem but it turned out to be a fault on the circuit board of the control module, thanks anyway"
I have exactly the same problem. When I have the cover off there is a red light on, from what I can tell is the "Over Heat Fan" this seems to keep the fan on, and because it is in error prevents the system igniting. Haven't got a solution yet it only happened last night. Stu.
Posted on Jun 12, 2010
Tips for a great answer:
Jul 26, 2013 | Cars & Trucks
Mar 23, 2012 | Heating & Cooling
Jul 12, 2010 | Heating & Cooling
May 04, 2010 | Heating & Cooling
Apr 12, 2010 | Heating & Cooling
May 12, 2009 | Heating & Cooling
Jun 01, 2008 | Heating & Cooling
Aug 21, 2017 | Heating & Cooling
549 people viewed this question
Usually answered in minutes!