Question about Plumbing
Your best bet is to get a replacement pump this is a common problem with this model
Posted on Jul 26, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Apr 22, 2017 | Plumbing
Jul 03, 2011 | Home
May 29, 2011 | Little Giant 554455 VCMA-20ULS 230V 20'
Thank you for posting your question here on Fixya.com.
Replace the check valve that is part if the discharge hose barb. When it fails the water trapped in the vertical section of the tube comes back into the tank and cycles the float on again causing what you describe. The best way to confirm this would be to watch the water level as soon as the pump shuts off and see if it climbs without any other source of water coming into it. If it is not rising then the issue is with the float itself and is not worth fixing; replace the unit in that case.
If this answer does not fix your problem, please comment with additional details prior to rating the answer. You may also contact me thru our website at www.arrowmotor.net. Positive feedback is appreciated once your problem is solved!
Feb 15, 2011 | Little Giant C20ST Condensate Removal Pump...
Sep 17, 2010 | Little Giant VCMA-15ULST, 1/50 HP, 65 GPH...
Jul 04, 2010 | Little Giant VCMA-15ULST, 1/50 HP, 65 GPH...
Apr 07, 2010 | Little Giant 554425 VCMA-20ULS 115V 20'
Sep 29, 2009 | Little Giant 115V 60Hz Condensate Removal...
168 people viewed this question
Usually answered in minutes!