Question about Reddy R155D Utility Heater
What kind of ignition is it? spark or hot surface igniter? the photocell just detects the flame. it causes the controller to go into lockout if it doesn't detect a flame. a hot surface igniter uses 120 volts to operate, again off the controller.
Posted on Nov 26, 2007
Deffently not the photo cell.the photo cell in this unit DOES NOT see the flame.it counts the light flashes from the flame.the circut board is more likely your problem.circut boards are around $90.00.if you have been changing ignitors at $50.00 pre shot it gets expensive.how much did you pay for the heater.also quick note your heater is a desa product....... desa is in bankrupsy at this time and parts are getting real hard to find.................
Posted on Feb 11, 2009
Tips for a great answer:
Oct 21, 2011 | Coleman Propane Forced Air Heater...
Here are a couple of tips that I wrote that tell you how to troubleshoot a Torpedo or Reddy heater...
Reddy Heater - Troubleshooting Torpedo Heaters
Feb 10, 2011 | Reddy Heater-170,000 BTU Kerosene Deluxe
Dec 14, 2010 | Reddy Heater-170,000 BTU Kerosene Deluxe
Nov 24, 2009 | Reddy Heater RLP100 Portable Forced Air...
Jan 20, 2009 | Reddy Heater-170,000 BTU Kerosene Deluxe
Jan 06, 2009 | Dayton E50 Heater
Dec 04, 2008 | Heaters
Dec 05, 2007 | Reddy R155D Utility Heater
317 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: