Question about LG Heating & Cooling
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Error C6 on lg cool art is common. you guy need a new CAPACITOR. cost $7.05c aud. it's 6uF 450vac.
take about less than 10min to install.
my lg model is lsz244vm-4, it's run well now.
Posted on Mar 04, 2008
The first thing i'll say is you will need to get it repaired by a technician and i strongly recommend you not to do it by urself.
Remote control units have diagnostic program in the
control, after 3 to 5 minutes of operating if the diagnostic
tools detect abnormal operation, then its shutdown the unit
to protect from damage. Thermistor sensor is one of the
parts that detect the operation of the unit. Out of range
or defective thermistor can shut the operation of the unit.
- If your indoor and outdoor is clean start the unit in cool mode and monitor the outdoor pipes. If your suction pipe is icing or dry then your unit is under charge, but if your suction is cold and sweating then the system is ok and sure that the thermistor sensor is defective.
- Out of range thermistor sensor in both return air and freeze up sensor can cause the tripping “off “ the unit.
Posted on Mar 22, 2008
Probably a capacitor in the either the compressor or outdoor fan. Don't know if they are dual capacitor or each has it's own. This is just according to the other posts on this site. I would call in a tech to have a look at it. Should be able to diagnose this in about 10 minutes.
Posted on Jun 09, 2008
SOURCE: Our LG Art cool Airconditioner
Inverter compressor run current high. Check compressor windings all equal 1 to 4 OhmsCheck to earth 50 MOhm minimum, check run current. If high, winding is weak. Solution: Replace compressor.
Posted on Jan 20, 2011
Tips for a great answer:
Jun 30, 2018 | LG Heating & Cooling
Jun 20, 2018 | LG Heating & Cooling
Feb 28, 2009 | LG Art Cool LA121HNP Split System Air...
Jan 05, 2008 | Computers & Internet
750 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: