Question about Amana Heating & Cooling
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
The reset button is located behing a panel on the front of the unit that is labeled Heat Reset. If that label is gone then look around, it is a small hole, small enough for a paper clip to fit through.
That being said, I have 137 of these units in one of my hotels and have not had a single one needing to be reset. You probably are going to need a new control board kit. These can be purchased from Amana. They are $130. Make sure that you have pulled the heater coil out and inspected it first. Also, there was a recall years ago where Amana was supposed to contact and send out new voltage switches. These are the round black things that the Brown heater wires connect to on the upper and lower side of the heating coil. You should also try to replace those if you find the coil in good condition. I have had those resolve heating issues. Most of the heating issues were a result of a bad relay on the control board though.
Please remember to rate this fix.
Posted on Feb 12, 2009
Sounds as though the power cord reset switch might be bad and need to be replaced. If not, then there is a short somewhere in the system. Do an ohms test on the switch to determine if it is bad.
Posted on Mar 17, 2009
the compressor is controled seperately from the fan, this is done with the thermostat, try turning the thermostat on then of or untill you hear the "click" sound from the thermostat. If the compressor is still not turning on this may be more than you can fix if your not familiar with electrical hvac troubleshoting... more than lilkely the thermostat may be bad, or your compressors starting components are failing...if the compressor is comming on when the unit is turned on you could have a freon leak causing no heat. hope this may help some there is just too much to write on the causes this will give you a start though!!
Posted on Jan 18, 2010
Tips for a great answer:
Nov 13, 2013 | Amana PTC153B50AM Split System Air...
May 14, 2011 | Amana PTH123B25AJ Heat Pump Air...
Nov 12, 2010 | Amana PTH153B50AE Air Conditioner
Jun 19, 2010 | Amana PTH093B35AM Thru-Wall/Window Air...
Jan 17, 2010 | Amana PTC153B50AM Split System Air...
Oct 30, 2009 | Amana PTC153B35AJ Air Conditioner
Mar 16, 2009 | Amana PTC153B50AM Split System Air...
Jan 23, 2009 | GE Zoneline AZ38H12DAD Split System Air...
Nov 02, 2008 | Amana PTH123B25AJ Heat Pump Air...
Jul 04, 2018 | Amana Heating & Cooling
169 people viewed this question
Usually answered in minutes!