Question about Electrical Supplies
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
that is strange
normally a 3 wire switch could only be able to control 2 things + off. black would be common, red would be one fan speed or set of lights and blue would be the other fan speed or set of lights.
if it is a replacement, couldn't you just hook it up like the switch you are removing?
most likely the black wires are grounds for everything and white would be power. hook it up however you like. white power would hook up to the black wire on the switch and then the blue to one light and red to the other set of lights white wires.
Posted on Jan 06, 2010
The red goes to R or rc and the blue would go to C or common sometimes its BK on the thermostat and the yellow would go to Y.
Posted on Jan 22, 2010
Incoming white - outgoing white
This is the neutral, which just passes through without connecting to the switch
incoming black - switch black the hot wire provides power to the switch
switch red - outgoing red a traveler, will have power when toggle is one position
switch yellow - outgoing black
the other traveler, will have power when toggle is in the other position
incoming bare - switch green - outgoing bare the switch is grounded and it passes through
If this was helpful, please vote.
Posted on Mar 23, 2010
OK .. the thick black and white are the power for the fan , are there also white wires on the lamp sockets ..??
The thick black wire should connect to the black wire on the switch.
The small black wires connect to the red and blue wire on the switch .. two small black wires each .. that should give you a position for 2 lights , and 4 lights, on the step switch .. but there should be white wires from the lamp sockets connected to the thick white from the fan .
please respond .
Please Vote !!
Posted on May 25, 2010
Testimonial: "I appreciate the response, which reinforced my thought process and it worked - Thanks!"
Find the Hot wire:
Your switch has 2 wires. One of these wires is Hot, and one goes to load. Disconnect wires from switch. Turn on power. Do not stand on wet surface. Test each wire to bare copper wire. When tester lights up, that is Hot wire. The other wire goes to load.
Hot wire goes to Black timer wire
Wire to load goes to Red timer wire
White wire connects to white wires that are twisted together
Bare copper wire connects to Green wire from timer
How to connect white wire to white wires that are twisted together.
a) Strip white timer wire so you have 1-1/2 " of bare wire. Stranded wire will wrap around other wires easily.
b) Remove wire nut. DO NOT UNTWIST wires.
c) Hold all whites together so bare copper lines up. Wrap stranded copper around the twisted wire.
d) Replace wire nut, or use larger wire nut. Twist real tight. Do not use tape. You can solder the connection.
e) When done, pull on white time wire to make sure it is held tight. Push whites back into box.
Posted on Sep 26, 2010
Tips for a great answer:
Dec 07, 2014 | Electrical Supplies
Mar 29, 2013 | Electrical Supplies
Dec 10, 2010 | Hardware & Accessories
Nov 13, 2010 | Intermatic Inc. EJ500C Digital Wall Switch...
Sep 25, 2010 | Intermatic Inc. EJ500C Digital Wall Switch...
May 21, 2010 | Hunter 27148 Remote Control
Nov 11, 2009 | Kitchen Appliances - Others
Jul 06, 2009 | Heath Zenith Occupancy Motion Sensor Wall...
Jun 15, 2009 | Hampton Bay 24002 Ceiling Fan
224 people viewed this question
Usually answered in minutes!