Question about Water Heaters
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
The water heater is locked out. The following process should reset it.
1. Reapply power to the water heater and wait for 3 seconds for the system self-diagnostic check.
2. Within the first 30 seconds, the temperature dial must be rotated back and forth crossing the 120
degree mark at least six (6) times. This will reset the control and display a normal flash code
Posted on Apr 20, 2009
Check the following:
See if your heater has a pilot gas adjustment valve. It should be on the gas control valve somewhere. Not all heaters have these. It will be a screw on the valve that can be turned.
Make sure the thermocouple sensing bulb is squarely in the pilot flame and also check that the fitting where the other end of the thermocouple connects to the main gas valve is tight.
Check the pilot gas orifice (where the pilot gas comes out) for carbon build up - you may need to remove the pilot gas line and thermocouple assembly to get to this. This problem is pretty common.
Check the gas pressure to the heater. Run the hot water in the dwelling until the hot water heater starts. Check the flame on the main burner and see what color it is - it should be blue with possibly some yellow-tipped flames. If not, there could be a problem with the gas pressure at the heater or venting. If the heater has a gas pressure regulator, it may be out of adjustment or defective.
Finally, and this isn't very common, the pilot light can be extinguished if there is a draft problem, usually associated with an issue with the flue pipe venting system for the heater or another nearby gas consuming appliance.
Posted on Dec 31, 2009
Testimonial: "thank you. will try these suggestions tomorrow. really appreciate it."
SOURCE: need reset code for richmond
I am poting this here hopefully it will help someone else. I have a richmond 40 gallon power vent water heater and it was not working. It was flashing 2-3 on the LED. I used this procedure and it started up..
you can reset the control by unplugging the blower during start up, leave unplugged for at least 5 seconds, plug back in and within 30 seconds cycle temp control from hot to low 6 times.
Posted on Apr 13, 2010
SOURCE: Hosed basement floor. soaked
Certain Rheem water gas water heater models feature electronic controls with a flammable vapor sensor installed on the bottom portion of the water heater unit. This sensor is designed to shut off your water heater system to prevent fires in case flammable vapors are present within the area. If your flammable vapor sensor caused your water heater to shut down, check the area immediately for leaking gas or other flammable products. Common household chemicals such as bleach can also trip the safety system as well as unsuccessful burner ignition attempts.
White Rodgers Intelli-Vent PowerVent Control Equipped Models
Posted on Jul 23, 2010
Testimonial: "Didn't know about the LRLL-RLRR code thing until I contacted the customer support. But you did get it right on........... just a little later. "
Tips for a great answer:
Jul 28, 2017 | Water Water Heaters
Dec 20, 2014 | Rheem Richmond 40 Gal Natural Gas 6 Year...
Nov 26, 2014 | Water Heaters
Sep 18, 2013 | Audiovox Richmond 6G40-36F 6-Year Tall Gas...
Apr 16, 2013 | Audiovox Richmond 6G40-36F 6-Year Tall Gas...
Mar 10, 2013 | Water Heaters
Jun 13, 2012 | Rheem 40 GAL ELEC TALL Water Heater 6YR SC...
Sep 04, 2011 | Audiovox Richmond 6G40-36F 6-Year Tall Gas...
Jul 23, 2010 | Rheem Water Heaters
Nov 18, 2017 | Water Heaters
61 people viewed this question
Usually answered in minutes!