Question about Heating & Cooling
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: Empire DV-215 Low Flame Issue
Either a restriction in the gas train, low gas pressure or a bad gas valve. Check the pressure on the gas line when on pilot and again when the burners are running. Depending upon what type of gas it runs on, you should have at least 4" W.C. if Natural Gas and 10" W.C. if Propane. If gas pressures test good and all valves are open, you are looking at replacing the gas valve.
Posted on Dec 10, 2007
Sounds like you have a wick that has burnt unevenly in the past and now there is not a good setting for an optimum burn. Either the wick needs to be trimmed even or you need a new wick.
Posted on Nov 14, 2008
The insert sounds like the cap covering the adjustment screw. Pin hole is for cap removal. Wondering why flame is so high?! Shouldn't have orange flame. If heater doesn't light with lower flame... thermocouple (thing that the flame heats up) may be bad.
Posted on Jan 03, 2009
Tips for a great answer:
Feb 27, 2013 | Heating & Cooling
Jun 01, 2011 | Williams (5009622) Ceramic Gas Wall...
Apr 27, 2010 | KitchenAid KGYS850LT Gas Dryer
May 06, 2009 | Procom ML300HGA Heater
Jan 16, 2009 | Desa International GWP20T GLOWARM Wall...
Jan 10, 2009 | Reddy Heater-10-12-15,000 Btu L.P.
Dec 02, 2008 | Reddy Heater RLP100 Portable Forced Air...
Nov 20, 2008 | Dyna-Glo D-E36 Infra-Red Wall Mounted...
Oct 06, 2008 | Dyna-Glo D-E36 Infra-Red Wall Mounted...
21 people viewed this question
Usually answered in minutes!