Question about Lochinvar Pool & Spa
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: pool heater Maintenance
It is vitally important that your water chemistry be maintained. Pool water that is acidic or alkaline will attack your heater's internal components in a relatively short time. A monthly (minimum) analysis by a reputable pool store will help you maintain proper water balance and extend the life of everything in your pool, be it pumps and equipment, ladders and handrails, marsite, paint or vinyl liner.
Posted on Jan 03, 2009
For some reason your heater is not recognising the flame when it goes on. The biggest reason for this will be small spider webs in the burner orfaces. These are on the main gas manifold where it connects to the burners. You can get a small wire and bend it to go in these orfaces but the first time you do this it will probally be easer to pull the tray and remove the orfaces from the gas line. Good luck, I hope this helps.
Posted on Nov 28, 2009
My boss once asked me if I could work on a Lochinvar. I told him I could pronounce it.
Chevy is a car and so is Mercedes Benz. Lochinvar is the same kind of German engineering. Quality product. Tough to find people qualified to work on one and pricey at that. Great heaters though. As far as the model I have only worked on the big ones.(commercial) I have found if you work on them one time they stay fixed.
Posted on Dec 01, 2010
Tips for a great answer:
Feb 05, 2015 | Lochinvar ENERGYRITE 250K BTU NATURAL GAS...
Jul 16, 2014 | Lochinvar ENERGYRITE 150K BTU NATURAL GAS...
Jun 29, 2014 | Lochinvar ERN402-LPASME - Pool Heaters -...
May 25, 2014 | Lochinvar ENERGY RITE 399000 BTU PROPANE...
Dec 07, 2013 | Lochinvar ENERGYRITE 400K BTU PROPANE GAS...
Dec 07, 2013 | Lochinvar Energyrite Residential Heaters...
The pressure switch is located in the front header, behind the
upper side jacket panel, above the water connections. When
required, the pressure switch can be reset with the following
1. Clean filter and skimmer.
2. Start filter pump.
3. Set digital thermostat to highest setting.
4. Turn the adjustment knob on the pressure switch clockwise
until the combustion air fan in the front control panel turns
off. Fan will not turn off if system pressure exceeds 5 PSI.
5. Slowly turn the adjustment knob counter-clockwise until the
combustion air fan turns on. Turn knob an additional ¼ turn
6. Turn filter pump off and on several times. The heater should
shut down immediately when the pump stops.
7. If the heater does not shut down immediately as the filter
pump stops, repeat steps 4, 5 and 6 until proper operation
8. Reset thermostat to desired temperature setting.
If after doing all of the above you still have the problem.... you can remove the switch and check for debris in the water passages. If you find debris remove it, reinstall the switch and repeat steps above.
- Still have the problem... Replace the switch.
Thanks for choosing FixYa,
Mar 21, 2011 | Lochinvar ENERGY RITE 399000 BTU PROPANE...
Nov 30, 2010 | Lochinvar Energyrite 402000 BTU Natural...
Feb 16, 2010 | Lochinvar ENERGYRITE 250K BTU NATURAL GAS...
Nov 05, 2009 | Lochinvar ENERGYRITE 400K BTU PROPANE GAS...
46 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: