Question about Heating & Cooling
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Red= power........White=heat.............Green=fan.................(grey)-(yellow)=cool .....these are the connectons. Disconnect these wires from the thermostat and know that red/power is the only wire that send power to the thermostat, and the rest sends it back to the unit to call for whatever,, red--to . white for heat... red to green for fan .... &red to grey for cool! OK! Turn all your power on, and use a jumper wire from red / green for fan and see if the fan comes on! Then move the jumper wire from red to green , to red / to white for heat and the fan , wait for 3 minutes before removing and going to the next step. Then red /to grey for cool and check if the outside comes on. Either you have a wire touching past the insulations and making a connection, a bad thermostat ,oe excessive wire lead touching the next connection.Thank you very much!
Posted on Nov 05, 2008
Make sure a back draft in the flue is not happening. Wind can blow it out until the flue heats up. The flame sensor may not be close enough to the burner flame. It may be weak and need to be replaced or if its an optical one it may be dirty and not see the flame very well. Its not wasting much gas but it puts extra wear and tear on the gas controls, is noisy, and, as you said, blows cold drafty air. A gas control system that has issues of any kind is not real safe. It needs to get fixed.
Posted on Jan 08, 2009
remove the blower unit it slides out on some gas furnaces you may have a control bord in the way if you dont have a goodman motor you will need a belly band to clamp to new motor to provide the mounting arms also after loosening the shaft set screw spray w wd40 turn on side and shake motor should fall out if gas furn 115v motor hope this helps
Posted on Jun 09, 2009
Yes. If the high limit is tripped, the furnace will bring on the fan continuously until the limit resets. Often, they will not reset if tripped repeatedly. If the furnace is too large for your application, you probably are not able to move enough air to keep the heat exchanger cool enough.
Posted on Oct 03, 2009
Tips for a great answer:
Jan 21, 2015 | Frigidaire PTAC Electric Heat 9000 BTUs...
Oct 08, 2013 | GE Carrier Bryant Payne 2.4 Hp...
Sep 17, 2017 | Amana Heating & Cooling
Jul 06, 2011 | Goodman CKL49AR49 Air Conditioner
May 04, 2017 | Heating & Cooling
Feb 17, 2010 | Storkcraft Baby Lennox Stages Crib
Jan 29, 2010 | Hayward 2HP Pool Pump Motor A O Smith...
Dec 04, 2009 | Humidifiers
Jun 09, 2009 | Heating & Cooling
40 people viewed this question
Usually answered in minutes!