Question about Water Water Heaters
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
New users get to try the service completely Free afterwhich it costs $6 per call and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: Hot Water Overflow
Do you have an expansion tank tank in the line leading into water heater? If not what is happening is that the water is no longer allowed to go back into the city supply. You said that you had turned it off while you left so the water heats up and has no place to go so the preasure/ temperature P/T valve opens and lets out the excess water from the expanded supply (heater water) that has no where else to go. It used to be that the extra expanded water just backed up into the supply pipe and back into the main. That is no longer possible in most places by the National Plumbing code. The answer may be to install the expansion tank into the incoming line. You can see then now at all hardware stores where water heaters are sold.
Posted on Jan 04, 2009
Tips for a great answer:
Jan 05, 2017 | Water Water Heaters
Jan 10, 2015 | Water Water Heaters
Oct 31, 2012 | Water Heaters
Aug 13, 2011 | Reliance /State Ind. 9002450 Element For...
Nov 23, 2010 | Rheem Tank Water Heater G100-200, 100...
Nov 08, 2010 | Rheem 40 Gallon FVR NATGAS Low WATER...
Oct 08, 2010 | Water Heaters
Dec 17, 2009 | RTO Atwood Water Heater - 6 Gal LP
Aug 21, 2009 | Rheem Water Heaters
Nov 16, 2017 | Water Water Heaters
40 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: