Question about Heating & Cooling
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: Carrier air conditioner problem
My Carrier unit did the same thing. It was low on refrigerant (Puron in my unit). I am worried I have a leak somewhere. Hopefully, it is not in the coil. The service call wasn't cheap either. Puron runs around $10-15 a pound and mine took several pounds to replenish.
Posted on Aug 03, 2008
there is a thermo-sensor switch next to the circuit board that tells the fan switch to turn on when the plenum is hot enough. this needs to be replaced.
Posted on Dec 16, 2008
sounds as if your low voltage transformer might have bit the bullet will need replacing all of the devices you mention are powered by this one low voltage t-stat
Posted on Jan 01, 2009
Hi, you have replaced the stat several times, and adjusted the anticipator so its not the stat.This is a split gas/elect unit, and working on these for many years and looking at some of the solutions given, they are right.You need to be looking at the Furnace fan control.Units of that age they do tend to stick open and run constantly.I doubt its the fan relay, maybe if you were in the cooling mode.Fan controls are not that expensive. You probably have a Honeywell 7" to 11" Probe, with the auto/manual button, with a temp dial to set you're on off temps. I would inspect the heat exchanger for any signs of cracks or bulging being its that old. If you find any, you are looking at carbon monoxided and should be thinking about an upgrade soon.Also flame roll out.I am thinking of you're safety is all.If you do have this type of fan control, there is a tab that has to be cut before you install for 24v. control.It comes set for 120v. and will burn out all of your 24v. componants.Those old Bryants will run for years. Good Luck!
Posted on Nov 14, 2009
Tips for a great answer:
Jul 20, 2015 | Heating & Cooling
Jun 18, 2014 | Dometic Rooftop RV Air Conditioner
Dec 02, 2013 | Dometic 3313192.000 White Single Zone LCD...
Nov 01, 2013 | Heating & Cooling
May 13, 2011 | Carrier 38CKC042 Air Conditioner
Mar 07, 2011 | Heating & Cooling
Nov 09, 2009 | Dometic Rooftop RV Air Conditioner
Jul 08, 2009 | Dometic Rooftop RV Air Conditioner
Sep 29, 2008 | Goodman Heating & Cooling
Aug 21, 2017 | Heating & Cooling
25 people viewed this question
Usually answered in minutes!