Question about World Heating & Cooling
If the furnace made a clicking noise trying to turn on and then makes the BANG noise at the furnace, it’s most likely a delayed ignition. Imagine a room full of gas and then someone decides to light a match. Big problem. That's what’s happening in your furnace if the ignition of gas is delayed.
A variety of issues can delay the combustion of that gas. So the gas builds up in the furnace until—BOOM—it ignites, causing a mini-explosion. This can harm the heat exchanger, which is very expensive part to replace. Some causes of delayed ignition includes:
1. Dirty burners
2. Flames are lifting away from the burner outlet due to too much primary air
3. Too much gas
If you're handy enough to understand what I've said then burners can be cleaned/replaced, and primary air can be adjusted. With some units gas flow can be adjusted as well; other times the gas valve will need to be replaced.
If you've no idea what I've described, GET HELP before you ruin the heat exchanger and have a more expensive problem on your hands or worse...
Posted on Dec 24, 2016
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
weak pilot flame: should wrap around therocouple.
blue flame with yellow tip not yellow and lazy.
if flame good replace thermocouple
Posted on Oct 26, 2009
SOURCE: Kozy World propane wall heater
The ceramic "bricks" need to be heated evenly. Since 3 are good, I would have to assume the other two have a restriction. Maybe a spider in the orifices, If you can access the "jet" where gas comes out, try using a paper clip or something similar to clear any blockage. If that wont do it, pull the burner, remove each orifice and clear. Good Luck
Posted on Dec 30, 2009
Testimonial: "Thank you very much for the info. There was some trash around the opening of the 2 jets. I cleaned them out with a tip cleaner and now it works fine."
Your model is not listed at http://www.kozyheat.com/.
If this is currently a natural gas fitted device, there is a better than not chance it can be converted.
Please check with the manufacturer or dealer where you purchased the device. You can also contact your local propane supplier who would do the actual converting of the orifices.
A note: If this device is presently set up for natural gas and is hooked up, and you still have natural gas available, this is normally the cheaper of the two fuels to use.
Thanks for your quesiton at FixYa.com
Posted on Jan 02, 2010
SOURCE: My pilot light on my
From what you have described there appears to be dust, dirt or pet hair in the pilot or the pilot tubing, as well as the Oxygen Depletion Sensor (ODS). OR your heater may be the wrong gas type. In other words, you have Propane Gas and the heater is a Natural Gas heater (or vise versa). Look for the manufacturers tag on the side or back of the heater. It will tell you the model number, serial number and gas type. Even with this, on rare occasions, the manufacturer's plate may be incorrect. The only way to be sure is to remove the front cover of the heater and look at the control valve. It should be marked LPG or NG.
Posted on Jan 28, 2011
Yes, it sounds like the third heater has a Control Valve problem. It's allowing more gas into the system than what it's supposed too. Have you tried turning the flames down to a lower setting? If so, did it lower the flame height? How old is this heater and is cleaned and serviced at least annually? Are you using Natural Gas or Propane?
Please get back to me with the answers to the above questions and I may can help you.
Posted on Feb 07, 2011
Tips for a great answer:
Dec 24, 2016 | World Heating & Cooling
Nov 17, 2015 | Kozy World World Marketing KWP324 Gas...
Apr 05, 2015 | World Marketing of America Kozy-World...
Mar 22, 2011 | The Companion Group Kozy World Portable...
Jan 31, 2011 | The Companion Group Kozy World Portable...
Oct 09, 2010 | Procom (177653) Utility Heater
Dec 30, 2009 | Heating & Cooling
Dec 09, 2009 | The Companion Group Kozy World Portable...
Oct 26, 2009 | The Companion Group Kozy World Portable...
Nov 15, 2008 | The Companion Group Kozy World Portable...
61 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: