Question about Heating & Cooling
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
ok...where to start.lol ....the thermostat is just a switch.It will tell the unit to run or not run.if you measure the temp with the heatpump running,the air is warmer than 68 but it feels cool to you because your body is 98.6.The unit will run more often and for longer periods when the temperature drops outside for a few reasons.First,your house has more of a load to heat,meaning you have more heat loss because of the difference in temperatures outside and inside.Second,your heat pump pulls heat from the outside air.The colder the air outside,the less btu's for it to pull.If you have anymore questions firstname.lastname@example.org Hope this helps,Dave
Posted on Nov 11, 2008
I would insist that Sears either have a Senior tech come out and fix it or return it to the state it was prior to them touching. Then call some one else. Have them involve the Goodman rep in your area.
Posted on Jan 20, 2009
Is this an electric or gass furnace - Eather of these can can have this problem its most recomendable that you call a seviceman .
in the case of electric furnace you may requier a new heat sequencer. And in the case of gass you may requier a new relay.
Posted on Feb 19, 2009
The outside fan should be running except when the Heatpump goes in to defrost mode. Then the fan stops with the compressor running and it switches the reversing valve to heat up the outdoor coil. That should last about 5 min and you may see steam come off of the outdoor coil. That's normal.
Is the compressor running? It's possible that it's stuck in defrost or the fan simply died. I hope this helps.
Posted on Feb 19, 2009
Tips for a great answer:
Dec 28, 2016 | Heating & Cooling
Sep 25, 2015 | Honeywell RTH8580WF WiFi Thermostat
Jan 10, 2015 | Emerson 1F89EZ-0251 Blue 2" Thermostat,...
Aug 24, 2014 | Honeywell Th5220d1003 Non-programmable...
Sep 15, 2011 | Heating & Cooling
Jan 24, 2011 | Honeywell Programmable Thermostat Heater
May 30, 2017 | Heating & Cooling
Dec 21, 2009 | Honeywell Programmable Thermostat Heater
Dec 11, 2009 | Goodman Heating & Cooling
23 people viewed this question
Usually answered in minutes!