Question about Heating & Cooling
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Behind the unit near the floor level, is a yellow wire with a black bulb at the end. This is the actual sensor for returning air. If there is cool air infiltrating the area where it is located, it will keep the unit running until the return air reaches temperature. You could also have a bad sensor but highly unlikely. Make sure there is no air infiltration influencing the sensor. Also, you can unclip the sensor and pull out a few more inches of wire to locate it higher up away from the floor. Tie it up with a wire tie.
Rinnai it testing a remote thermostat but as of yet, there is no plans to offer one.
Posted on Nov 26, 2007
I bought mine last summer. Used it once or twice. Hooked up it today and it is a piece of ****. Been at 34celsius for the last 4 hours and still not even close to being cool .. and its in my bedroom
DON'T BUY DANBY portable a/c -----------
Posted on Jun 07, 2008
See the link on the Danfoss site. This has helped me http://heating.consumers.danfoss.com/xxNewsx/5dbcb2f9-e888-4d2d-9761-7470786749c9_CNP1.html
Posted on Dec 09, 2008
One of two things you can try. Do you own a volt ohm meter? Anytime your unit cycles short like it is doing the control circuit which on this one is 24 volts that engages relays and controls the gas valve to open and close. I am thinking the heat exchanger is getting so hot it is tripping the upper limit which for the most part is around 180 degrees. So next time it turns off take your ohm meter and with the power to the whole unit off. Either turn the breaker off or there is a light switch that is real close to unit turn it off. Undo the two wires to the gas valve and ohm them out. You should have continuity if you get nothing check each limit switch should have a couple. Undo wires to them and check. If you find one that is open more then likely the upper one. They are a safety device that keeps the unit from getting too hot.
There might be another option increase the speed of your fan motor to get the heat out of furnace quicker. Look at the circuit board notice the fan wiring going to it. The Red wire from fan is low speed look to see if it is on HEAT on the board. You should have 4 speeds to pick from you could take the black off of COOL and swap wires and test the unit by doing that. I'm going to put a solution on this so I can come back to it quicker. Even though we a just testing it for now. ken
Posted on Dec 21, 2008
Tips for a great answer:
Sep 21, 2016 | WHITE-RODGERS DIV 1F78-151 White 70 Series...
Feb 09, 2015 | Heating & Cooling
Oct 29, 2013 | Honeywell Heating & Cooling
Dec 28, 2012 | Honeywell Programmable Thermostat Heater
Sep 22, 2010 | Honeywell Programmable Thermostat Heater
Apr 02, 2010 | Honeywell Programmable Thermostat Heater
Jan 03, 2010 | White Rodgers White-Rodgers 1F85RF-275...
Jun 12, 2009 | Honeywell Electronic Programmable...
May 09, 2008 | Honeywell Electronic Programmable...
Oct 20, 2017 | Heating & Cooling
39 people viewed this question
Usually answered in minutes!