Question about Heating & Cooling
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Red is usually hot side of transformer,yellow is for the a/c compressor,white is for heater,green is for the blower fan,now the blue could be energize for heat or the common side for the transformer,brown can also be the common side of the transformer. It sounds like you need the blue wire connected to the common side for the thermostat....but be careful. Some units use this as a energize wire and are not a common. I would find out what furnace model you have then look online and double check what this wire is or you could damage the new thermostat and/or the 24 volt system on your fau. And also always have the power to the unit disconnected so you do not ground a circuit.
Posted on Oct 03, 2009
Have you checked to make sure the batteries are, in fact, good and that they are facing the right way? If so, it's time for a new thermostat.
Posted on Oct 04, 2009
Tips for a great answer:
Apr 09, 2014 | Honeywell Programmable Thermostat Heater
Mar 02, 2017 | Heating & Cooling
Jan 07, 2018 | Honeywell CT87B ROUND HEATING&COOLING...
Oct 24, 2009 | Honeywell Electronic Programmable...
Oct 10, 2009 | Honeywell Electronic Programmable...
Oct 01, 2009 | Honeywell Electronic Programmable...
Mar 22, 2009 | Honeywell Programmable Thermostat Heater
Jan 14, 2009 | Honeywell Programmable Thermostat Heater
Dec 17, 2017 | Honeywell Heating & Cooling
72 people viewed this question
Usually answered in minutes!