Question about Heating & Cooling
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Bad Safety valve. (valve w/red button). Thermocouple keeps the magnet open to keep pilot and so gas can flow to burner. Make sure pilot is clean and strong and hitting thermocouple. If it doesnt stay lit replace Safety Valve.
Posted on Dec 17, 2008
I would change the thermocouple and here is why:
The thermocouple is the pilot's, well, co-pilot! It is the electronic device that senses if the pilot flame is hot enough to sustain burning the gas fuel from the burner. If the thermocouple thinks it's safe, then it keeps open the main gas valve located in the pilot assembly. If the thermocouple does not sense enough heat from the pilot flame (such as when the pilot is out), then the thermocouple shuts off the gas valve to the burners.
How the Thermocouple Works
So what is this thing and how does it work? Well the thermocouple (technically called a thermocouple junction) is a device that contains two metal wires welded at the ends and placed inside a protective metal case. The thermocouple sensor is found at the business end of the pilot flame and is designed to be placed in the hottest part of the flame. The other end is connected to the pilot valve body. As the thermocouple heats up, it produces a small amount of electricity and when it gets hot enough from the pilot, send a signal to open the gas valve by using a solenoid operated by a 24 volt transformer. The thermocouple calls the shots, and by converting heat to an electrical signal, it allows the gas valve to open or close. Once the gas valve is open, gas is then constantly supplied to the pilot and as required for the gas burners (as called for by the thermostat). If the pilot goes out, then the thermocouple gets cold and produces no electric signal to open the gas valve's solenoid and the gas valve shuts off the gas supply to the pilot and burners
Posted on May 27, 2009
if burner lights after jumping valve you have something wrong in thermostat loop. disconnect the 2 thermostat wires on gas valve and use multimeter on continuity setting. if all wires ,connectors and components are good,you will get a tone.since you have jumped out each component in thermostat loop with no success ,i would suspect a bad wire or oxidation on a terminal .
Posted on Sep 24, 2009
Probably a bad solenoid in the gas valve. Higher voltage of a new thermocouple keeps it open longer but it still fails over a period of time. Look into a new gas valve for the water heater.
Posted on Dec 17, 2009
Tips for a great answer:
Sep 08, 2015 | Water Water Heaters
Jun 25, 2014 | Jandy Lite 2 Natural Gas Pilot Light...
Jan 10, 2013 | Heating & Cooling
Dec 19, 2012 | Heating & Cooling
Apr 22, 2012 | Teledyne Laars Teledyne_ Laars Lite2...
May 25, 2009 | Heating & Cooling
May 05, 2009 | Bosch & Tankless LP Hot Water Heater
Jan 15, 2009 | Reddy Heater RLP100 Portable Forced Air...
20 people viewed this question
Usually answered in minutes!