Question about Goodman Heating & Cooling
Sounds like either a stuck relay or stuck contactor. Not a difficult fix if you have right part. Turn power off and locate how high voltage gets to the heat strip. If there is a black box on a circuit board than it would be that whole piece.
Posted on Dec 20, 2016
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
May 18, 2015 | Goodman Manufacturing Goodman GPH1330M41...
Dec 22, 2014 | Goodman Heating & Cooling
Dec 16, 2014 | Goodman Manufacturing Goodman Gas Furnace...
May 21, 2014 | Goodman 3 Ton 14 ee Goodan Heat Pump...
Feb 01, 2013 | Goodman Heating & Cooling
Jul 08, 2012 | Amana Ptac Heat Pump Control Board Kit...
May 30, 2011 | Goodman Heating & Cooling
Apr 02, 2010 | Goodman CLQ36AR49 Air Conditioner
Jan 03, 2010 | Goodman PHKJ048-1 Air Conditioner
Jun 09, 2008 | Goodman GMS90703BXA Heater
35 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: