Question about Heating & Cooling
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: furnace won't stay running
Furnace fails to operate.
• Integrated control module
diagnostic LED is
flashing ONE (1) flash.
• Furnace lockout due
to an excessive
number of ignition
“retries” (3 total)1.
• Failure to establish flame.
Cause may be no gas to
burners, front cover
pressure switch stuck open,
bad igniter or igniter
alignment, improper orifices,
or coated/oxidized or
improperly connected flame
• Loss of flame after establishment.
Cause may be
interrupted gas supply, lazy
burner flames (improper gas
pressure or restriction in flue
and/or combustion air
piping), front cover pressure
switch opening, or improper
induced draft blower
• Locate and correct gas
• Check front cover
operation (hose, wiring,
Correct if necessary.
• Replace or realign
• Check flame sense
signal. Sand sensor if
coated and/or oxidized.
• Check flue piping for
length, elbows, and
• Verify proper induced
draft blower performance.
Posted on Nov 25, 2008
first off buy yourself a honeywell stat, in my personal opinion lux stats are garbage, I have run into so many that are bad stats !!! but as far as your fan not shuting down, sounds to me like your fan center on your circuit board is bad and will not shut down the fan when needed, you will have to replace the circuit board, as the fan center is a part of the whole of the circuit board, hope that helps
Posted on Jan 20, 2009
The two most common reasons I have found for this are listed below. You have already addressed the third one.
1) Grounding issue. This can be difficult to find but easy to diagnose. Try using a volt meter or even just a piece of wire. Touch one end to an unpainted surface of the interior furnace cabinet and the other end to the sheet metal plenum or other ground. If the symptoms go away then you have diagnosed the problem and need to find the faulty ground.
2) Pressure in the flu. Check to make sure that the flu vent pipe is not clogged or even partially filled with debris. The small rubber hose that connects to the switch from the inducer blower motor may be clogged. Also check the orifice on the inducer motor side. You can clear this with a paper clip. Water (condensation) in the inducer motor housing or pressure switch can cause a failure too. Rarely is the pressure switch itself bad. This usually will only happen if it has been physically damaged or soaked. Best of luck.
Posted on Jan 29, 2009
Hello, it sounds like your Furnace might be shutting off due to your high limit switch.A limit switch will open when the furnace overheats due to low airflow, . check air filter, clean blower wheel, and check to make sure the blower wheel is running at proper speed and not dragging sometimes cause by a weak capacitor. Anything that restricts airflow will cause a limit switch to open.
Posted on Mar 08, 2011
bad primary control (the box with the reset button), maybe your thermostat but unlikely. Try the Primary Control first. How old is your burner?
Posted on Dec 14, 2012
Tips for a great answer:
Mar 14, 2014 | Atwood 38591 Excalibur XT Furnace 1522 15K...
Jan 04, 2013 | Heating & Cooling
Nov 04, 2012 | Heating & Cooling
Jan 03, 2011 | Ruud Heating & Cooling
Apr 09, 2010 | Heating & Cooling
Nov 03, 2009 | Goodman GMS90703BXA Heater
Apr 25, 2009 | Heating & Cooling
Jan 19, 2009 | Coleman Propane Forced Air Heater...
Nov 19, 2007 | Heating & Cooling
24 people viewed this question
Usually answered in minutes!