Question about Heating & Cooling
Forgot to mention it is an approx. 20 year old Keeprite
Flame sensor is a small rod sitting on the opposite side from ignitor. It is on the "flame" side of the gas tubes and usually to the far left or right, whichever is opposite your ignitor. Held in place by one 1/4 inch screw.
Posted on Dec 19, 2016
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Feb 12, 2015 | Reznor Hanging Furnaces-Power Vented-...
Dec 26, 2013 | Heating & Cooling
1. Thermostat calls for heat. 2. Draft inducer motor starts. 3. Pressure switch attached by a small plastic or rubber tube senses the negative pressure produced by the draft inducer and closes. 4. Draft inducer runs for 30 seconds to a minute before you hear a gas hissing sound. The ignitor did not glow, the flame sensor (a small metal probe about 1/8" in diameter, with a white porcelain base) does not sense the flame, so after 8 to 10 seconds the hissing sounds stops with no ignition of gas to heat your home. Your furnace shuts down and goes into a lock out condition until you turn your power switch back off and on again. Then the sequence starts all over again with no ignition of the gas. Solution:You probably need to purchase and install a new ignitor. I would suggest that you inspect your ignitor closely for cracks. Make sure you do not touch the ignitor with your bare hands. If you do not visually see a crack, then you could have a furnace control board problem or a limit, rollout switch problem. The furnace's control board might not be supplying the voltage to the ignitor.If your furnace lights and the gas stays on for 8 to 10 seconds, then shuts right back off, then you need to clean your flame sensor with light sand paper or steel wool. You might need a new flame sensor, but most of the time they can be cleaned an will work well after cleaning.
Dec 11, 2010 | Mr. Heater Natural Gas Garage Heater -...
Jan 27, 2010 | Honeywell Electronic Programmable...
Jan 19, 2010 | Honeywell Electronic Programmable...
Dec 10, 2009 | Heating & Cooling
Nov 23, 2009 | Heating & Cooling
Jan 25, 2009 | Honeywell Focus 6300B 5-2 Days...
Jun 18, 2018 | Heating & Cooling
117 people viewed this question
Usually answered in minutes!