Question about Heating & Cooling
You have to narrow further. 230 in to board, 230 out of board with no contactor, 230 to the contactor with no load, 230 thru contactor with a load. Likely the board, not sure what you are using the contactor for. If its a heater than you possibly have a bad limit switch or bad element.
Posted on Dec 17, 2016
Testimonial: "Barrel contractor on Taylor 706 ice cream mach"
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
New users get 2 Free calls (no credit card required) and instant help on almost anything you can think of (from cars to computers, appliances, handyman, and even pets).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Feb 03, 2014 | Midea Heating & Cooling
Jan 25, 2013 | Epson Stylus Photo R300 InkJet Printer
Jun 27, 2012 | Goodman Heating & Cooling
Feb 21, 2012 | Welding Tools
Jul 14, 2011 | Heating & Cooling
May 17, 2011 | ICP Vortex Fan Timer Control Board For Air...
Jul 04, 2009 | Heating & Cooling
May 23, 2009 | Weather King 10AJA3001AH Air Conditioner
Jan 31, 2009 | Heating & Cooling
41 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: