Question about Heating & Cooling
You have to narrow further. 230 in to board, 230 out of board with no contactor, 230 to the contactor with no load, 230 thru contactor with a load. Likely the board, not sure what you are using the contactor for. If its a heater than you possibly have a bad limit switch or bad element.
Posted on Dec 17, 2016
Testimonial: "Barrel contractor on Taylor 706 ice cream mach"
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Feb 03, 2014 | Midea Heating & Cooling
Jan 25, 2013 | Epson Stylus Photo R300 InkJet Printer
Jun 27, 2012 | Goodman Heating & Cooling
Feb 21, 2012 | Welding Tools
Jul 14, 2011 | Heating & Cooling
May 17, 2011 | ICP Vortex Fan Timer Control Board For Air...
Jul 04, 2009 | Heating & Cooling
May 23, 2009 | Weather King 10AJA3001AH Air Conditioner
Jan 31, 2009 | Heating & Cooling
Jun 24, 2018 | Heating & Cooling
41 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: